Jason took great care of us, very happy with his service.
17JUN2022 Jason B Arrived for new customer no cool. spoke with homeowner about the issue they donâ€™t know but itâ€™s just not cooling. Inspected system found 3 14x24 filters very dirty, and condenser coils plugged up. Evap coil is in okay shape. Cycled system at the thermostat and moved to AC. found AC tripped on thermals. With customer permission I changed all the filters with fresh customer provided filters. and washed the condenser coil. Reset thermal overload switch system is cooling properly at this time. We decided to go ahead and get this equipment on a maintenance plan. Please give us a call if you have any questions or issues in the future. It was great meeting you two!
Arrived with gas valve prior technician had diagnosed. Install gas valve. Leak checked pipe. Adjusted gas pressure to 3.45 w.c. Temperature rise in range. Performed silver club furnace maintenance. Capacitor and motor amp draw in range. Induced draft motor in range. Cleaned flame sensor and tested ignitor. Cycled unit multiple times to insure that all safeties are working and unit running as designed. Replace batteries to thermostat. Found water on top of furnace flue was leaking due to some issues with prior service call I sealed flashing at no charge to customer. System is heating at this time. Customer had 25.00 gift card I applied towards balance.
I arrive for a silver membership no cool call. I first spoke with the homeowner and found that they have turned the system off day before when they were not home. I first inspected the condenser and checked all electric components in the system. I then inspect the indoor system located in the attic of the the masters bedroom. I inspected the evaporator and all electrical components in the furnace. I checked the system temperature drop across the furnaces and evaporator coil. I check the systems refegerant charge and found the system to be running at 9.8deg superheat and the system called for 10 deg superheat. I cycled the system on and off and found no issues with this system at this time. I do recommend to add or increase the return duct to help recirculate air in that section on the home. I recommend to give the systems some time to cool the masters bedroom area down. I found no issues with this system at this time. If you have any problems please contact us and we will be right out
I arrived for a non member no cool call. I first inspected the system located in the garage closet and found the system to be running properly. I inspected the condenser and found the coils to be compressor stopped up. I checked all electrical components and found no issues. I check the system refrigerant charge and found the the system to be running low on R410A. I recommend to preform a leak search to find the leak and see what we needed to do to fix the leaking area or component. The homeowner declined to just add what refegerant was was necessary to get the system running properly. I cleaned and added 5LBS 2OZ of R410A to the system and set the systems subcooling at 12 deg. I told the homeowner that they will have this problem again if the leak is not found and fixed. This system is running to the best of its abilities at this time.