We enjoyed Brett’s wonderful service. He explained each detail carefully and made our AC problem easy to understand. Brett and his assistant were also very friendly and kind! We’ll definitely use them again in the future!
Great Service and a very respectfully technician. Thanks for coming out so late!
Got my AC working again! Will use Hart Heating and A/C again! Thank you!!
Got here fast and fixed a potential big problem!
Mike Tyson did a great job repairing our AC. He was prompt, courteous, and honest. He explained the problem, offered solutions and the price. I would highly recommend Hart A&C and Mike Tyson.
Very professional. Diagnosed and fixed problem really fast.
Fantastic company! Fast service! We are very pleased and grateful!
Annual heater tune up and maintenance
Found defective defrost sensor on Lennox heat pump, replaced sensor and cycled unit multiple times in heat and cool to confirm operation is correct at this time.
Did a preventative maintenance on an Amana 90% gas furness, cycled multiple times in heat to check operation, cleaned flame sensor and blower motor, and check motor bearings. Waxed and cleaned unit and is working properly at this time.
Annual heater maintenance
Preformed maintenance on commercial Carrier gas furness cleaned and cycled multiple times to confirm system working
Annual heater maintenance.
Tune up on Carrier gas furnace, checking safeties, operations and for gas leaks and for Co in supply air. Changed filter and cleaned flame sensor. Tested heat rise, blower operations and electrical.
Installed a Goodman furnace and coil. And a 3 1/2 Goodman condenser. We upgraded the electrical distribution. Installed a new whip and pad. And added vibration dampers under it.
Drain line repair
Installing a Goodman 4ton 16 seer heat pump condenser with a matching air handler upgraded condenser with turbo dual capacitor, and a hard start compressor kit, on the air handler put a float safety switch on the pan and re built some of the primary drain that needed it.
Repaired electrical distribution problem on this condenser got it running check the Freon cleaned and washed it out.
Tune up and service on multiple systems
Repaired a carrier that was not working properly. Had a bad electrical distribution in it. Replace some of the defective parts got it operating
Indoor repair on control system
A/c control repair