Lennox AC not cooling. Dual capacitor swollen and bad. Install new dual capacitor
Change out Carrier 14 Seer heat pump.
Perform free second opinion. Test all capacitors, motors. Performed leak check to amana system. Found leak at condenser unit. Customer has decided to replace condenser with 16 seer carrier condenser.
Diagnostics on AC system. Compressor failed. Capacitor replacement
Trane AC maintenance. Replace contactor, filters and hard start kit