Great service and will be calling smith from now on if any problems. Thanks
Very professional . Resolved problem. Would use again.
I am completely satisfied with the work done on my units.
Fixed in one visit with good price
Did service call on Lennox unit and replace filter.
Replaced duel run capacitor. Checked unit.
Did service call on Lennox generator and did yearly maintenance.
Found shorted breaker on Carrier unit.
Dual run capacitor discharged. Replaced and checked ptac unit.
Found evaporator coil plugged. Cleaned. Run capacitor below threshold replaced.
Cleared drain and performed maintenance agreement on Lennox system
Did service call on carrier unit and replace capacitor and added Freon.
Replaced dehumidifier control board. In warrenty.
Did service call on Lennox unit and replace evap coil checked out system for yearly maintenance agreement.
Replaced shorted breaker. Checked unit.
Did service call on Lennox generator and replace vaule cover.
Did service call on Lennox unit and added Freon and sealed air vent.
Performed full system check on 4 units
Did service call on Frigidaire unit and replace blower motor and control board and tstat.