Very informative, very polite
👍 Repaired drain tray, & installed 1# Freon. Thanks
He did a great job.
Inspected & repaired AC Unit as required. Thanks
Dallas is a very pleasant young man and also knowledgeable in his work.
Final inspection on a new system.
Not cooling. Bad expansion valve
Cleaned evap coil in place. Sealed return around the door and adjusted freon charge
Code 416. Bad outdoor coil temperature sensor
Water leaking. Broken drain line.
Replaced condenser fan motor
Not cooling. Dirty evaporator coil
Unit not cooling. Bad Condenser fan motor an low ambient control
Linnux no cooling- Fixed