Logan was very professional, and was able to fix our AC very quickly. We were very satisfied with the service and will definitely use All Seasons again.
Service call was prompt , called 30 minutes before arriving . He was polite and courteous explained so we understood . Very pleased and would recommend highly.
Complaint of a.c not cooling. Found system with open run circuit due to bad run capacitor. Replaced run capacitor and tested system. System is now showing normal operation at this time.
Complaint of upstairs system not cooling. Found o.d fan motor common lead disconnected causing no o.d fan operation or cooling. Solutions- Landed common wire and tested system. Ran well within rated amperage. System showing normal operation at this time.
Complaint of indoor unit condensate pump stuck humming. Diagnosis- Found pump clogged with dirt and debris causing pump to fail. Solution- Cleaned and repaired pump and done full system checkout. System looks good at this time.
Complaint of no a.c, outdoor unit cycling but indoor fan not coming on causing low pressure trip/lockout. Diagnosis- Found system with incorrect thermostat wiring causing no call for fan. Solutions- Rewired system and thermostat and system is now showing normal operation at this time.
Planned maintenance checkout on Goodman a.c system. System looks good at this time.
Complaint of furnace still throwing pressure switch failure. Diagnosis- Found systems fule exhaust holding water on a sag or sloped upwards part of pipe causing intermittent pressure switch failures after extended periods of use. Solution- Cut pipe back and added new 90° 3inc elbow and made sure pipe had proper slope now. Tested system and showing normal operation at this time
Planned maintenance heating checkout on two York diamond 90s, high efficiency furnaces. Main system checked out great, downstairs system needed burners replaced or cleaned. Pulled and cleaned burners, tested system afterwards and conducted l.p gas leak search. Both systems now showing normal operation at this time.
Checkout on goodman air conditioner.
Replacing control board on goodman electric furnace.
Working on a Colman electric furnace that is making a loud noise
Checking the heat on a gas furnace and an electric furnace.
Doing a loop flush on a geo thermal heat pump that was collapsing the lines due to air.
Install customer supplied thermostat and do routine maintenance.
Perform tune ups on heating and air conditioning systems
Emergency service on Lennox air conditioner in Spokane mo