Arrived at location on 10/1/21 - Found bubbles in site glass and pressures low. I added 404A to fill site glass and bring pressures to normal. I pumped down unit and checked receiver level and found to be good. Unit was at negative 6 when I left and working properly.
Arrived at location on 10/1/21 - Arrived on site found wires exposed on power cord, pulled power cord and stripped back wires, reconnected power cord and turned unit on no further issues.
Arrived at location on 8/30/21 - Left side hotter than right side. Checked temp is good. Also checked flue is clean. Gas preasure at 4 in wc. Found vent holes clogged in back is for ventilation. Cleaned now ok. Also advised to remove thick aluminum in bottom and keep tin foil out fan. Operation ok at this time.
Arrived at location on 8/27/21 - Checked thermostat and sometimes it was sticking. Replaced thermostat and checked superheat which was high. Opened txv and got superheat to 6 degrees. Also this is a keg cooler. And the alcohol got warm and takes a very long time to cool back down so unit is constantly running causing it to ice up. Let manager know I’m on call if it acts up again.
Arrived at location on 8/26/21 - Water pressure at 40 psi, drops to 20 when turned on, takes awhile to fill. Filled unit, brought up to temp, tested unit ok. Advised to raise pressure.
Arrived at location on 8/16/21 - Valve was very clogged at drain. Pulled valve apart and cleaned. Pumped oil back up no leaks at this time.
Arrived 7/16/21 - Temp at 350 but only 200. Talked to marshal at factory, said to change probe. Probe is bad will order. If don’t correct problem, then control is bad. Returned to location on 7/20/21 - Pulled probe out new one is too short . Talked to Dave at factory sent pictures to him he has to research it and find part is old fryer. Returned to location on 7/23/21 - Installed new fryer, checked dc milivolts and set at 550, checked gas pressure and set at 4”. No further issues.
Arrived at location on 7/12/21 - Removed existing exhaust fan for grills. Installed new exhaust fan that was already on the roof. Connected and verified proper rotation. Existing exhaust fan is too heavy to take off the roof myself and I need another man. Tom and Joe to return tomorrow a.m. to remove.
Arrived at location on 7/7/21 - Found t-pile bad. Replaced, brought up to temp. Set pilot to 500 mv. Operation ok at this time.
Arrived at location on 6/16/21 to check water lines. Water turned off. Turned on, flex hose was leaking. Removed line and used other line and change fitting. Turned on water and turned on units. Brought up to temp, tested ok. No leaks, operation ok at this time.
Arrived at location on 6/6/21 to check on walk in freezer. Unit not running, checked time clock and it checked out ok, Found broken wire that shorted on the heater, repaired and watched unit come down to temp. System is operating properly at this time.
ARTIC AIR REACH-IN COOLER - 04/19/21- Tom-Started unit and found compressor not coming on Found compressor to be bad, talked with Denny at united Harrisburg and he will get back to me about price and availability of compressor, I will update when he gets back to me. ** Service Manager Matt will quote for a new unit.
SCOTSMAN ICE MACHINE - 4/6/2021-David W - found unit turned off upon arrival. removed front cover and seen that the light was not on for full sump and water was overfilling. removed water level sensor and found it scaled up. pulled it apart, cleaned it and reassembled. light came in showing full sump now. after the 2nd cycle the water started overflowing again. found water inlet valve was stuck open. will need to order a water inlet solenoid valve and replace. as for now I have machine turned off and water is shut off behind the machine. 04/19/21- Tom-Replaced water inlet valve and ran one batch of ice, Unit is working properly at this time
Surveyed Pressure fryer unit, needs new solenoid valve and coil, high pressure relief, power switch. Needs basket handle. Will order parts and return. Not safe to use. Needs fixed by 9/15/20. Will need to clean drain, from solenoid to front drip pan. Plus need to test pump and filter system when fixed. 8/28/20 Replaced Relief valve, solenoid valve, power switch, boil out, set gas to 3.64 in wc. Left handle, Customer also bought 2 gas regulators off my truck for his maintenance guys. Completed.
Arrived. Dishwasher unit was running. checked and rinse temp wasn't making. found pressure set at 25. adjusted down to 20. ran and unit dropped to 145 for rinse temp randomly. swapped rinse thermistor for booster thermistor and unit is warming ok at this time. will order replacement thermistor. along with new contactors. unit working ok until we return. 8/20/20 Installed contactors and probes. Ran unit, checked amp draw. Missing leg, found fuse blown at disconnect. Got new fuse from Mike. Now checked at 25 amps. Ran uni,t tested ok.