Excellent service, very knowledgeable and professional
Zach was very knowledgeable and fixed the problem we had.
Very knowledgeable and very friendly
Logan did a very complete job checking our systems. I feel like he went above and beyond and wasn’t in a rush to go to the next job. They worked around our busy schedule and stayed in constant communication. Excellent A+
Zack did a very good job of testing our HVAC systems and thoroughly explained the work that he performed. He is friendly and cheerful and is dependable. Thank you, All Seasons Comfort Systems!
Really enjoyed talking with Zach. Seemed very knowledgable about the product. He was able to answer every question that I posed to him. I asked his opinion on a few different things and recieved what i believe was good information from him. That's why we didn't have to give it a lot of thought in order to go with All Seasons. And best of all he served our Country in the USMC!
Very pleased, Logan does a wonderful job.
Logan is a very nice knowledgeable. Very helpful & explains everything that needed to be done & costs and ways of saving me money.
Good job thank you for the quick service and his honesty
Doing a Planned Maintenance Agreement heating tune up on a Goodman heat pump package unit. Replacing air filter. Checking coils for cleanliness. Checking blower for cleanliness and operation. Testing 10KW emergency heat strips. Checking temperature split. Tested defrost operation. And tested thermostat operation. Fixed a future problem on wiring that was starting to rub through. Which would have caused the unit to short out and have issue’s operating. Fixed wires and secured away from metal.
Planned maintenance checkout on Rheem heat pump system. System checked out great at this time.
Performing two dual fuel heating checkouts, on a planned maintenance agreement for two Lennox systems. Replacing air filters. Replacing humidifier pad and testing operation. Checking coils for cleanliness. Checking refrigerant charges. Testing electrical components and defrost. Performing combustion analysis’s on furnaces. Checking temp rises. Inspecting burners, flames sensors, and igniters. Checking flue pipes. No issues found on todays checkout.
Replacing leaking indoor coil
Working on a temp star heat pump that is not cooling due to a failed capacitor
Working on a Lennox heat pump that is leaking due to a plugged drain
Troubleshooting a no cooling call on an Amana A/C. Found outdoor unit running only the fan and not the compressor. Verified compressor would not start. Disconnected power and checked the 45/5 dual run capacitor. Compressor side (45) had failed, and was bad, causing compressor to not start. Replaced 45/5 capacitor under warranty. Checked amp draws and system operating. System now cooling properly at this time.
Starting a planned maintenance agreement on a Rheem heat pump system. Inspecting air filter, replacing if needed. Washed out outdoor unit and coil, removing leave buildup on bottom of unit. Spraying indoor coil to help remove dirt/debris buildup. Cleaning drain line. Checking refrigerant levels. Testing outdoor electrical components and checking amperage’s. Verifying correct thermostat operation. And checking overall system performance. No issues were found at checkout.
Troubleshooting a Lennox variable capacity communicating heat pump that lost communication with outdoor unit. System showing critical alert and not running. Added 24v transformer to outdoor unit to remedy 12v DC and 24v AC voltage bleed throughs, to eliminate lost communication signal on old thermostat wiring. Tested system after repairs, no issues present.
Troubleshooting a no heat call on a heat pump system. Blower running and no heat. Found outdoor unit with no high voltage to system. Found breaker at breaker panel in the off position from remodeling. Breaker was not labeled. Labeled breaker and checked over system, no issues found.
Installation of new lennox heat pump system.
Working on a minisplit that is not heating properly
Performing a heating tune up on a Nordyne heat pump system. Replacing air filter. Testing emergency heat operations. Inspecting indoor unit wiring. Checking system refrigerant charge. Testing outdoor electrical components. Inspecting outdoor unit wiring. Testing defrost functions. Testing thermostat operations.
Replaced lennox air handler control board due to low voltage short internal to board. Got new board installed and set up and tested. System showing normal operation at this time.
Complaint of no heat on gas furnace system. Previous company diagnosed bad draft induce motor. Diagnosis- Found inducer wheel bound with debris to side of flu pipe. Solution- Removed restriction and tested system. System working properly at this time.