Logan did a very complete job checking our systems. I feel like he went above and beyond and wasn’t in a rush to go to the next job. They worked around our busy schedule and stayed in constant communication. Excellent A+
Zack did a very good job of testing our HVAC systems and thoroughly explained the work that he performed. He is friendly and cheerful and is dependable. Thank you, All Seasons Comfort Systems!
Really enjoyed talking with Zach. Seemed very knowledgable about the product. He was able to answer every question that I posed to him. I asked his opinion on a few different things and recieved what i believe was good information from him. That's why we didn't have to give it a lot of thought in order to go with All Seasons. And best of all he served our Country in the USMC!
Very pleased, Logan does a wonderful job.
Logan is a very nice knowledgeable. Very helpful & explains everything that needed to be done & costs and ways of saving me money.
Good job thank you for the quick service and his honesty
Did a great job, no problems found
Planned maintenance check out on two lennox heat pump dual fuel systems. Both systems checked out excellent at this time.
Installing a new zone sensor on an l comfort zoning control.
Doing tune ups on 3 heat pump systems.
Doing a tuneup on a Lennox heat pump system
Doing tune ups on 2 Lennox heat pump systems
Amana heat pump not cooling, customer says it quit sometime lastnight. Diagnosis- Found system with shorted run capicitor due to chipmunk. Solution- Replaced capicitor and checked charge and amp draw of motors. System working great at this time.
Complaint of water leak and system not keeping up. Diagnosis- Found homeowner to have drain line cleared, also found system to be low on charge- low delta t and low subcooling. Solution- Did summer tune up, added 3lbs of r410a got subcooling to lennox recommend setting and temperature drop up to 19°. System looks great at this time.
Giving a price to wrap the ductwork in a crawlspace
Performing a planned maintenance agreement AC checkout on two systems. One Amana AC with gas furnace and a Lennox dual fuel system. Replacing air filters. Cleaning coils. Cleaning condensate drain lines. Inspecting and testing electrical components. Checking system refrigerant charges. Testing thermostat operations. And testing overall system performance.
Ac start up on new install
Performing a planned maintenance agreement AC checkout on a Lennox heat pump system. Changing filter, cleaning components, testing electrical components, checking system charge, and looking at overall system performance.
Bidding a replacement heat pump system.
Complaint of no heat. Found low voltage fuse blown due to aged contactor and a few bare low voltage wires on heat pump low pressure wiring. Replaced contactor and insulated and straped wire up from any metal. Tested system and showing normal operation at this time.
Performing a heating tune up on a Lennox heat pump system. Checking emergency heat, zone system, coils and blower for cleanliness, replacing filter, clearing condensation drain, checking charge, and looking at system performance.
Performing heating tune ups on two Lennox heat pump systems, under a planned maintenance agreement.