usually shows up within the hour, most times have part on truck, not a "special order".. Finally a great service company!
Commercial Coffee Machine Repair. I was called by a client in need of repairs on their commercial coffee machines. I arrived and discovered limescale buildup. A thorough descaling process ensured the machines consistently brewed coffee for the client’s business.
Commercial Kitchen Equipment Repair: I addressed an issue of inconsistent pizza crusts being produced by the client’s commercial dough press. With precision, I adjusted the dough press's settings and performed a comprehensive service of its components. With these adjustments, the system was back to great working order in no time.
Commercial Meat Slicer Repair. A deli's meat slicer wasn't slicing evenly. I inspected the blade and discovered it needed sharpening. After sharpening the blade, the slicer efficiently produced consistent and uniform slices of meat for sandwiches.
Commercial Walk-In Freezer Installation. A restaurant expanded its storage needs and required a new walk-in freezer. I expertly assembled the panels, installed the refrigeration unit, and ensured proper insulation and sealing. The freezer was now ready to preserve ingredients at the ideal temperature.
Commercial Ice Cream Machine Installation. An ice cream parlor needed a new commercial ice cream machine installed. I positioned the machine, connected it to power and water lines, and calibrated the freezing settings. Thorough tests confirmed efficient ice cream production, delighting customers with creamy frozen treats.
Commercial Kitchen Appliance Repair Service near Philadelphia Ave. A client contacted us for repairs on their commercial bread slicer. Upon inspection, I discovered a worn-out blade that needed replacement. I replaced the blade, calibrated the slicer, and conducted tests to ensure precise and consistent bread slicing. The owner was relieved to have their bread slicer functioning optimally again.
Commercial Garbage Disposal Installation near Wayne Ave. Collaborated with a client to install a commercial-grade garbage disposal system. Assessed their specific needs and recommended a suitable unit. Installed the garbage disposal, ensuring proper connections to plumbing and electricity. Tested the system for functionality and efficiency. Provided instructions for proper usage and maintenance. The client was pleased with the efficient waste management capabilities provided by the new commercial garbage disposal.
Commercial Refrigerator Repair Service near E King St. We were contacted by a commercial kitchen that had an inoperable refrigerator unit, which posed a great risk to the business. We promptly arrived at their location and proceeded to examine the refrigerator system to determine the cause of the performance issues. The examination uncovered the source of the problem to be a faulty compressor. I replaced the compressor to get the business' refrigeration system back up and running quickly, ensuring the preservation of perishable goods. The client was appreciative of the quick response time and the efficiency of the repairs.
Commercial Kitchen Repair Service near Norland Ave. When a commercial client encountered difficulties with their commercial steamer, they reached out to us for repairs. Responding promptly, I arrived at their place of business and assessed the issue with the steamer. After a thorough investigation, I identified a build-up of scale and minerals from hard water as the root cause of the problem. I diligently cleaned the steamer, removed the scale and build-up, and proceeded to replace the filters on the appliance to prevent such issues from recurring. We also scheduled regular maintenance services for their commercial kitchen equipment.
Provided a Quote near N Main St. I offered a comprehensive, transparent, and cost-effective quote to a commercial client seeking maintenance service for their commercial kitchen equipment.
Commercial Kitchen Equipment Maintenance Service near Main St. I arrived at the client’s location to undergo their annual Commercial Kitchen Equipment Maintenance Service. I examined the refrigeration and freezer units for signs of wear and cleaned the condenser coils on the systems. I then inspected the hinges and door gaskets to ensure they were clean and working well. I then replaced all of the filters in the appliances and cleaned the grease buildup from the fryers and oven.
The internal temperature of the reach-in freezer too warm. Found ice buildup on the evaporator coil and noticed the compressor runs constantly. Replaced the compressor and ran the defrost cycle. Tested to ensure freezer is cooling to proper temperature after service.
Arrived at location on 7/26/22 - Removed and replaced bad compressor, charged unit with 250 psi nitrogen and let stand for 30 minutes with no drop in pressures. Vacuumed system below 500 microns and charged unit to factory specifications. Waited for unit to cycle 3 times and is operating properly at this time.
Arrived at location on 4/26/22 - Investigated holding cabinet not heating. Found heating element burnt off. Will order new element and return to install. Returned to location on 6/17/22 - Replaced heating element and temp probe holders and grommets. Tested operation to be working as it should at this time.
Arrived at location on 1/31/22 - Found bad contactor for circuit E. Pumped unit down and checked operation of pressure control and it is cycling off at 5 psi with a 15 psi differential. Checked operation of both units and fans are running and unit is dropping in temp properly. Checked receiver level and it is about 25%,called Jeremy Fry and spoke with him and he would like us to hold off on topping unit off with 448 a refrigerant. The circuit F is also low on charge and will need topped off. Customer supplied the contactor.