RO system no longer producing water. Suggest replacing unit.
Called out for leak at ASV. Found no leaks at this time.
Leaking disposal in kitchen sink. Customer will replace disposal themselves.
Replaced 50 gal hybrid electric heater heater. Rerouted hot and cold water lines. Rerouted 3/4â€ condensate drain line. Rerouted P&T relief line. All work per Ron Bott.
Performed diagnostic found unit running. No issues found at this time units are 11 years old. Recommend start kits and power protection. Declined at this time.
Performed acm. Start amps at 112 rated for 104 recommend start assist kit. $303 on club membership. All else operating to spec at this time. Exit temp 53. Insulation at 6 to 7 inches recommend 8 inches of insulation to get at 13-15 inches $2,325.
Performed acm. Start amps a little high recommend start assist declines at this. Cleaned outdoor coil. Temp split 25.
INSTALLED NEW EVAP COIL UNDER WARRANTY
XC25 LENNOX AC PURCHASES 2 UNITS WITH VARIABLE SPEED FURNACE