Rheem/ Lennox hp
Lennox Lrp pac
Install a 4 ton pack unit heat pump. Added a partial piece of 10’inch flex. New grill, titan thermostat, surge protector and air scrubber. No tar added due to new roof replacement projecting coming up.
Installed new heat pump split
Rheem pac unit
No heating call failed outdoor txv
Install a 4 ton grizzly split system.
Performed diagnostic. Found burnt out wire from board to VAD. Fixed and checked amp draws. Unit is operating to spec at this time.
Performed diagnostic found low on charge. Charged unit with 410A and put die and sealant in system.
Performed diagnostic found bad VAD and exhaust motor. Recommend repairs or replacement of unit.
Performed install audit need to schedule time to return and install to filter grills 20x30. And 20x40. Installed old stats was not happy with new ones.
Performed acm. Checked amp draws and cleaned outdoor coil. Found indoor coil dirty recommend coil cleaning. Denied at this time.
Performed maintanence found VAD with loose terminal. Recommend replacing at cost of labor. Attic insulation is at 7 inches recommend adding 7 to 8 inches.