VERY LATE SHOWING UP BUT THE OFFICE DID CALL AND LET ME KNOW
Very friendly and knowledgeable
I have been pleased with the work done by the company, and pleased with the attitude and behavior of it's employees. I would and will recommend the to anyone.
Earl was a pleasure to have at our home. He was very efficient, kind & comfortable to be with.
The technician, Clemente Leal, has great experience. He told us what he was going to do up front. We would like to see him again.
Unit not cooling. Sunday service call. Found herm wire from board to phase shifter burnt and frayed. Replaced wire. Fixed ends of other wires. So issue will not happen Again. Unit now cooling. Labor and repair under warranty. Warranty and diagnostic fee.
Stat was not on the wall correctly. Customer pushed it down and started working. Unit running fine. Call canceled
Check unit. Low on 410a. Added a few pounds to get unit to cool. Unit has dye in system. Could not see oil or dye. King valve caps were loose. Recommend running unit and if happens again, perform leak search. Unit cooling at this time.
Post inspection. Tightened king valves and shradder caps, added 410 to spec so home will cool and heat correctly. Re sealed transition in closet. Fixed drain line so when back up happens it will trip float switch. Sealed around drain line coming from coil so air is not leaking. Unit cooling at this time.
Perform tuneup on Lennox unit for ACM member. Installed power protection in attic and performance upgrade to compressor. All systems operating within manufacturers specs at this time.
Ac tuneup on Rheem split unit
Ac tune up on Rheem heat pump
Perform tuneup on trane rooftop unit for ACM member. All systems operating within manufacturers specs at this time.
Ac tuneup on a York heat pump
OEM evaporative coil replacement part does not come with factory installed TEV as the original factory installed coil did... part in will call at trane to be picked up and installed tomorrow, customer approved.
AC tune up on 2 Rheem split heat units
Perform tuneup on rheem rooftop unit for ACM member. All systems operating within manufacturers specs at this time
The cu still had an animal and animal feces all in the cabinet, advised customer Iâ€™m not gonna work on a unit that has a wild animal dead or alive... once the animal is removed we would return to complete the repair of the unit.
Post inspection. First condenser inverter went bad. Sam had replaced condenser. Customer is very happy with the new unit. Home cools fast quiet. Unit cooling at this time.
Put tar around pvc drain. Unit operating to spec. At this time.