Earl did an outstanding job checking our ac system. Best service man ever!!!
Earl is the most thorough service technician I have ever encountered in my 40 years of home ownership. I trust him implicitly.
The guys came in and we’re professional and very proficient. I recommend their services to anyone. Thank you
Failed compressor. Probably time for a new unit
Tech was on time and effective
Excellent, professional service!
Diaz and assistant performed a routine inspection and condenser coil cleaning as directed. He suggested that the refrigerant may need a recharge, because it could be as much as 50% below standard, and recommended a refrigerant charge that would be between $500 to $900. Because the cooling operation appears to be adequate, and there are no other deficiencies, I don't have enough evidence to allow this procedure. I would never pay that much for a refrigerant charge without verification that it is substantially low. He also suggested that they would perform additional services for several thousands of dollars, if the 11-year old A/C system was newer.
David and his helper showed up on time and did a great job.
Trane heat pump summer maintenance
Carrier heat pump summer maintenance
Carrier summer check
Goodman heat pump summer maintenance
Goodman air conditioning summer maintenance service
Quality inspection of new Lennox system.
Customer has been approved with Greensky for 7,500. Will pay balance with credit card of $1,492.00
Lennox air conditioner summer maintenance
Trane air conditioning summer maintenance
Packaged Rheem unit not cooling