Found system low on charge. Discovered leak at the liquid line connection on the coil. Recharged system 3lbs. Added an inline safety switch to the upstairs furnace. Recommend adding a switch to the downstairs furnace. The customer would like to wait. Recommended adding start kits to both Condensers. Recommend adding air purifiers to both Furnaces. Signed up on membership for both systems.