Complete 1 system a/c repair and preventative maintenance check. Customer is moving shortly so will not be renewing. Found pressures for system very good. System is draining condensate properly and filter is clean. Customer had issue with freezing at evap coil due to dirty filter it is imperative to keep filter clean so that system can breathe. As of now system is running good.