Cost to replace heat pump. Install condenser on the ground
Performed air conditioner maintenance on Bryant unit
Annual maintenance check on a Bryant air conditioner
Annual maintenance check on a Lennox air conditioner
Replaced bad gas value on Bryant furnace
Noisy inducer motor
Heat pump frozen
Furnace repair on no heat situation. Found failed inducer motor bearings and replaced unit today. All is well.
Inspected heat pump operation
Replaced fan limit and blower motor on a Reznor unit in customers garage
Annual maintenance check on a Bryant furnace with humidifier service. Customer had the Iwave air cleaner added to system.
Annual maintenance on a Bryant furnace