Good Service. No complaints.
Emergency / Exit Lights and Portable Extinguishers Inspection
confirmed with Rob for afternoon Annual Sprinkler
Sheetz Store #: 369 Issue: fire ext from sink area was used Incident #: 10296755 Store Address: 2260 Route 119 Highway South, Homer City, PA, 15748 Store Phone Number: 724-479-3790
Emergency / Exit Lights Repair
During the recent sprinkler system inspection performed by Liberty Fire Solutions, LLC the following deficiencies were found. 5 year internal inspection due per NFPA on sprinkler system NFPA 25 REQUIREMENTS FOR 5 YEAR TESTING: 126.96.36.199 Alarm valves and their associated strainers, filters, and restricted orifices shall be inspected every 5 years unless tests indicate a greater frequency is necessary 188.8.131.52 Check valves shall be inspected internally every 5 years to verify that all components operate correctly, move freely and are in good condition 184.108.40.206 An assessment of the internal condition of piping shall be conducted at a minimum of every 5 years in accordance with 220.127.116.11 for the purpose of inspecting for the presence of foreign organic or inorganic material 18.104.22.168 Internal examination shall be performed at the following minimum four points: (1) system valve (2) riser (3) cross main (4) branch line NFPA 25 22.214.171.124 Gauges shall be replaced every 5 years or tested every 5
Annual Sprinkler Inspection Annual Extinguisher Inspection (4) ABC Annual E-Light Inspection
Annual Extinguisher Inspection Equip Desc: (2) ABC(s)