Arrived at location on 11/15/21 - Installed new fan blade. Applied some epoxy to the press joint on both sides to see if this helps with the longevity of the actual fan blade. I couldn’t find any other options to swap out with when I went to united as all the other motors were a lot larger in diameter with that shaft size. Will see how this works and if it does we will need to do this when we install them in the future.
Arrived at location on 8/5/21 - Evaporator was iced up and fans not running. Located UNMARKED WALK INN FREEZER condenser on the roof and put unit into defrost, Checked heaters and time clock. Clock was moving freely and seemed to be operating properly. Unit pumped down properly and contactor is ok. Removed remaining ice build up and started unit, fans would not come on so I checked power and found bad defrost termination switch. Once replaced fans came on once evap temp was low enough. System is operating properly at this time.
Arrived at location on 6/25/21 with part. Removed old one and installed new vacuum pump and hooked back up and checked operation, ok. Tested ok and got good vacuum.
BUNN COFFEE MACHINE - 04/26/21- Joey- Found unit not brewing and overflowing. head spray head clogged with scale. descaled spray head and unit. brew several batches checked all operation all ok.
WALK IN COOLER - 04/19/21- Tom - Door hinges are worn out and need replaced, Door hinges are reach in hinges, Customer would like a quote on replacing existing hinges and a quote on actual walk in hinges and regardless of what hinge he decides on he would also like a door closer installed on top of door. 04/21/21 - Voided Invoice & Refunded credit card sale (Billed in error)
Traulsen Reach-In Freezer - 04/13/21- Dave-Found unit breaker tripped. Removed wire cover and unhooked compressor then reset breaker. Unit stayed on. Tested compressor relay and found relay faulty. Ran to supply house for replacement relay and capacitor. unit is up and running fine at this time and dropping in temp.
Came in and installed new gas valve and thermopile on Bakers Pride Oven, tested the unit, unit heats up okay.
Removed harvest assist assembly and replaced with new part. Turned on Ice machine and found numerous other issues. The water was trying to start but couldn't. Once the pump motor was freed up, The compressor would not start. Tapped on the Ice cube relay, Contactor pulled in and compressor started. The Contactor is pitted and buzzing. Any of these components could fail at any time. Spoke to the facility manager about these issue and he asked to have all the parts quoted, and also quote a new machine. Managers information is attached in file room. Any quotes should be sent to him.
Found Walk-In Freezer compressor not running because unit was out on its internal overload, because condenser fan motor is not working and blade came off, Motor not available until tomorrow at United Harrisburg, I disconnected compressor so evaporator fans could still run, customer is okay with waiting unit tomorrow for part. 2/28/20 Replaced condenser motor and unit came on and is getting down to temperature, Unit was at 20 degrees when I left but compressor is making a wining noise unit is working properly for now but compressor may go out at any time and if it does due to age of condenser unit the whole unit should be replaced, customer would like price on replacing condenser unit, pics of data tags attached.
Arrived on site and Reach-In Cooler unit was unplugged. turned unit on. 134a pressures were okay. Compressor did not kick on right away. Compressor ran and shut off when calling for it to be on. it kicked back on after 20 seconds. I could only duplicate it once. compressor running at 5.85 amps and was hot, It also is running mildly rough. I did not replace evap coil due to 134a charge being okay and other issues with the reach in. I found that the temp settings were at 32 degrees. the cabinet probe does not shut off at 32 but at 26. it has a 8 degree differential which may be freezing unit up and causing the issues with the box. recommending new temp and defrost probes. I adjusted temp to 38 degrees with 6 degree differential to keep it above freezing. follow up call to verify proper operation. 12/30/19 Customer would like quote for new unit before any more work is performed. Sent Matt pic of data tag and info. Please attach a copy of quote to Melissa.firstname.lastname@example.org
Reach-In Cooler Compressor was off most likely from long high temperature alarm. Restarted and unit ran. Suction pressure was low and compressor very hot despite temperature being 70 in box. Added gas and leak checked. Unit has a very small leak in evaporator coil. We can quote evaporator coil replacement.
Call Out-I found a long string of paper towels wrapped around the blower wheel of Blended Ice Machine, throwing it off balance. The motor and wheel had shifted off center, so I re-centered them and screwed them in place. I removed the towels but it did damage to the motor bearings and on start up it makes a grinding noise. The exhaust fan is working for now but it should be replaced. I will get pricing and work up a quote.
per customer the pilot was not staying lit on the right oven side. checked the thermocouple, starting to get weak. put new thermocouple in and tested the unit. unit is cycling off and on. I had to wait 15 minutes when I got here to wait for customer since he was serving students. tested the unit, operation okay.
Checked Coffee Machine unit and found low water flow to tank. Checked fill valve, dispense valve and all hoses and connections. Found right side check valve between fill valve and tank stuck partially closed. Removed and tried to free check valve would not work, will need replaced. 9-6-19 Returned with part. removed old check valve from the right side and installed new check valve. checked operation of unit, okay. customer said the left side was not brewing right either. found that the brew port was blocked with lime. cleaned out port and checked operation, okay. both sides were brewing the same level. also installed customer supplied filter. checked all operation, okay.
returned with parts for Combi Oven. removed old heat exchanger and burner and installed new burner and heat exchanger. set gas with flue gas with meter. checked operation and ran a final rinse to wash out. all operation ok. burner and ignitor came with the heat exchanger. customer going to keep ignitor as spare. will return the rest of the parts.