Very prompt and professional.
Prompt and knowledgeable
Customers old faucet wasn’t working. Installed new Moen single handle chrome bathroom faucet that we supplied.
Performed leak detection for customer. Located leak on 3/4 copper line in water heater closet. 3/4 line ran from behind water heater over to manifold behind middle bathroom. Customer stated he will be performing re-route on his own. Capped line for customer and noticed customer had a second leak over between kitchen and 1/2 bathroom. Strongly recommended customer get a whole house repipe. Customer will be looking at between 13,000-15000 for whole house repipe. Customer does not have much attic access so line might need to be ran exposed on tiled roof or exposed under roof over hang.
Customer received a notice that the water heater needed a new thermocouple. Inspected water heater which was installed in 2008. Recommend replacing soon.