Brian is a very experienced Tech. Likeable, easy to listen to when explaining what he's doing. Very good Job Thank You
Marlon is like an encyclopedia of fire protection, his calm demeanor and straight forward reporting is irreplaceable. This is the second Facility I have had NW Fire in and Marlon continues to be awesome!.
This is the second property that I have used NW Fire for both fire alarm and fire sprinklers. Jesse has always been helpful and professional but then again I don't think I have met a field tech that isn't great.
Brian FA service Cody FA service Replaced all batteries except main facp . Need 2x12v18ah nut and bolt type on return trip on 5/17 please allow time for that. Those batteries were not staged Mounted hangin smoke detector No access to directors room add time to fix that on return trip on 5/17 Confirmed all mag doors release power. Doors are getting hung up on carpet. See pictures Trouble shot elevator not recalling. Confirmed it is not the module that is the issue. Called tech support to walkthrough programming and they said the computer software is needed and unable to do group programming through keypad. This is a IFP-1000 proprietary panel we don’t have software for. Need certified dealer to fix programming.
Annual Fire Alarm, Backflow, Sprinkler, Pre-Action, Fire Pump, Fire Extinguisher, Semi-Annual Kitchen Hood & FM-200 Inspections Deficiency for Silent Knight IFP 1000 FA-1 / 1st Floor Behind Hotel Reception Inside Front Office Door: 4th ,3rd, and 2nd floor north tower elevator lobby fire doors did not close. Hands up on the carpet Deficiency for Ansul R102 KISUP-5 / Panasia (Kitchen): Disregard Deficiency for Silent Knight IFP 1000 FA-1 / 1st Floor Behind Hotel Reception Inside Front Office Door: Batteries are due: Silent Knight VIP Main FACP: Qty 2 12V 18AH Bolt Type Silent Knight VIP Booster Panel under FACP: Qty 2 12V 8AH Silent Knight SK-4 Shed Panel FACP Qty 2 12V 8AH By Room IT5 Qty 4 Silent Knight 5895XL Qty 8 12V 8AH Deficiency for Ansul R102 KISUP-5 / Panasia (Kitchen): PANASIA HOOD- 1) wires in control head need to be installed in a junction box outside of the unit. 2) system failed to trip via fusible link line. 3) salamander oven does not have any nozzle covera