I have been using NWfire for 10 years they always do a great job for me.
Been using NW Fire for several years now at my properties. They are ALWAYS very professional and pleasant to work with. Wouldn't use anyone else. See you next year!!
Great job Marlon.
Very polite and personable young man.
I HIGHLY recommend NW Fire!!! They have patience of a saint!! GREAT TEAM!!
Hi I was very happy with Marlon Jones service and would use him again – thanks!!
Elevator Shut Trip Test Customer to arrange Elevator company
Deficiency Repairs Repaired fire main backflow preventer and retested
Deficiency Repairs Repaired domestic backflow preventer and retested
Annual Sprinkler, Hydrant and Fire Pump Inspection. Follow CFP Instructions
Annual Backflow Inspection Follow CFP Instructions
Sprinkler Repair Deficiency for Dry SPK-8 / L2 North: (3) dry sprinkler systems are due for a full wet trip (approximately 10 low point drains per system)
Brian FA service 4 hours Bldg A trouble shot all devices in vault and redid all connections. Can read open circuit and EOL from panel side of circuit . Panel still in trouble . There was a ground fault upon arrival I cleared the ground fault. It must be the module shorted out when vault was flooded see pictures for Siemens model. Need Siemens tech to replace bad module and check programming Bldg D nac panel trouble, located nac with fault. Traced wire manually from circuit one to located faulty appliance. found bad horn strobe in basement closest to sprinkler room . Removed horn strobe and bypass for now to clear panel until replacement is installed Siemens please see pictures for model type
Annual fire alarm inspection Annual Fire Alarm and Fire Extinguisher Inspections
All elevator smoke detectors recalled properly, 2nd floor & hoistway smokes did not report to fire panel.