very professional and was on time
Quick and effectient
Small job, but I felt just as important as a customer on a large job.
The service was quick and staff were very knowledgeable and friendly.
Jesse explained everything, very knowlegable.
Annual Sprinkler and Fire Alarm Inspection.
Deficiency for Wet SPK-1 / New Customer: Need to install Knox locking FDC caps (2) Northwest of building (4) Southwest of building For(6) total Deficiency for Dry SPK-9 / New Customer: Dry sprinkler system # 3 has a Reliable B-1 that did not operate and needs replaced. Deficiency for Dry SPK-11 / New Customer: Dry valve will not reset per customer. Did alarm test only. Need to replace dry valve #5 Reliable model C2 6” Take out is 19” Quick opening device was shut down upon arrival Reliable B-1 needs replaced Deficiency for Dry SPK-13 / New Customer: Dry sprinkler system # 6 has a Reliable B-1 that did not operate and needs replaced. Annual Sprinkler and Private Fire Hydrant Inspection
3-Year Full Trip for (1) Dry System
Annual Backflow, Fire Alarm, Sprinkler and Fire Extinguisher Inspection
Annual Sprinkler and Fire Alarm Inspection
Annual Sprinkler Inspection No one on-site to sign left vm with sam open completion of inspection