They were very adaptable and helpful during the entire process.
Grant is a capable, friendly professional tech. for N.W Fire.
Ryan Arrived early and quickly resolved the issue.
NW Fire Systems built our sprinkler and alarm systems. They have also done a great job maintaining these systems for over a decade.
I don't know the cost.
Good Company to work with. They are pros and get things done. Highly recommended.
Colby and his team made quick work inspecting and testing our entire fire system including sprinkler head inspections in 134 occupied units.
Very professional, courteous, accommodating; transparent in communication at every stage of testing. Would recommend to any building needing their fire and life safety inspection. Pricing was also competitive versus competitors.
Larry & Zeke are good at what they do. Very polite and professional.
Annual Winterization/LPD -
Annual Fire Alarm Inspection (25% of Bldg Floors 8-basement),Quarterly Sprinkler Inspection 100% Flows and Tampers
Annual Winterization, Fire Pump, Standpipe, Fire Alarm Central Tower Flrs B-4, East Tower Flrs B-4, North Tower Flrs B5-4 and West Wing - Flrs H-C; Semi-Annual Kitchen Hood, FM200; Quarterly Sprinkler Inspection (100% Flows and Tampers)
Quarterly Fire alarm and Sprinkler Inspection
Emergency Fire Alarm Service Call found problem on a nac circuit on floor two of north building and returned panel to normal status
AES hard wire zone 3 is general supervisory. Found tamper in pizza kitchen riser with water partially closed. It is right next to a prep station and probably gets bumped a lot. Restored panel to normal recommend putting a very tight chain lock on it so it does not accidentally get bumped. See pictures