Installed new 2.5-ton Carrier gas system. Installed new Honeywell thermostat. Installed new plywood overlay. Installed new filter base. Installed new gas shut off valve. Rebuilt and insulated condensate drain line. Added SS2 safety float switch. Cleared and treated drain and verified operation. Transitioned to supply plenum and sealed with mastic air lock. Installed new filter dryer, pressure tested with dry nitrogen and pulled a vacuum on the copper line set. Replaced disconnect and whip at outdoor system. Verified system is to factory spec. System is working properly at time of departure.
Found system not operational due to safety feature tripped. A breach in the heat exchanger is suspected due to common failures with furnace safeties. I also found a large buildup of rust in the system. Client would like to speak to our Comfort Consultant regarding replacement options.
Performed maintenance on two gas systems. A complimentary clean was performed in both interior cabinets and systems are now operational.
Installed new Mitsubishi mini split. Ran line-set and drain but need to return and finish copper. Will return next week to complete work.