Ray called and was able to come out even earlier than scheduled and within a short amount of time was able to diagnose our problem. He was very friendly and professional and gave us several different options to consider for the repair. He explained the pro's and con's of each option. He got us back up and running quickly. We are very pleased and this is why we use Garner for our HVAC needs!
The technician was very professional, knowledgeable, and on time.
Pleasure as always.
Don my technician was very knowledgeable and professional!!
As part of the maintenance package, Don came and inspected my ac system to make sure it was in tip top shape. He was very professional and gave me some tips for ways to keep my system running at peak efficiency.
Very knowledgeable, friendly and professional!
I’ve used Garner for a new AC, maintenance, and service and they have great technicians and service.
Indoor Noise /Vibration from unit.
Clean the coil and blower wheel system is clean now and working perfectly.
System inop. diagnostics needed.
Duct cleaning with blower cleaning as well.
Diagnostic on a commercial 3 phase Carrier Split system.
TXV carrier Heat pump replacement. Charged with new refrigerant.
Performed 1 system cooling tuneup on a straight cool system. Checked compressor and outdoor fan motor, checked contactor and capacitor, cleaned condenser coil, checked blower motor shaft and bearings and purged drain line. Inspected master bedroom for proper airflow.
Cool system check. Spring preventative maintenance on a Carrier split AC system.
Today we are cleaning a system to improve performance and comfort. It will also increase the lifespan of the system.
Performed 1 system cooling tuneup. Checked compressor and condenser fan motor, checked contactor and capacitor, cleaned condenser coil, checked blower motor shaft and bearings and purged clogged drain line.
Found and replaced a bad capacitor in the outdoor unit. Checked system operation and AC was working at completion of service
Diagnostic on a Goodman split AC system. Replaced a bad capacitor
Diagnostic on a Carrier Split system AC. Found refrigerant leak on the indoor evaporator coil.
Installed 3 to. carrier infinity system
Installed a new 3 ton carrier system, condenser and furnace / coil replacement.