Amana ASZ14 Pump 3 Ton. Install new air handler on new stand. New disconnect installed at air handler. New flex supply in closet. Install t6 pro thermostat. Breakers changed according to size. Condensor installed on pad block pad. Customer would like Bailey to email her a letter for her insurance company regarding the lightning damage that led to the unit needing to be replaced. Customer satisfied!
Upon arrival customer showed me the ac unit that need to be tuned up. The evap coil is clean. Clear the drain line with nitrogen and water. Checked all components for proper amp and voltage. Went to the condenser and checked for proper amp and voltage. Found a contactor with Pitt marks and a capacitor bad. Replaced the contactor and 35/5 capacitor with a turbo 200. We have a delta t of 18
Upon arrival customer showed me a ac unit that needed to be tuned up. Checked the evap coil and it was clean. Replaced customer supplied filter. blower is clean. Checked all amps and voltage. The UV bulb is burnt. Cleared the condensate with nitrogen and solvent. Check the condenser. All amps power and Freon level. Everything is working ass it should. Replace UV bulb under Warranty.
Upon arrival found system running and cooling. Inspected systems operations. System had a 21 degree delta-t and electrical components checked out. Left system in working order.
Upon arrival found pressures low, performed leak search. Found leak in condenser coil. We need to call to quote on the condenser coil. Once they have the price they might want Corey to come out and give and estimate on replacement due to cost. They wanted us to add refrigerant. Added 3 pounds of 410a refrigerant. Left system in working order.
Upon arrival found thermostat batteries in backwards. Switched batteries and tested operations. Left system in good working order.
Amana ASX16 AC 3 Ton. Install 3 ton air handler on new stand. Install uv light. New nest thermostat. Breakers changed to 35 amp. New condensor on new pad. Unit charged to subcool. Customer satisfied!
Technician went over system operations along with checking on electronics and refrigeration no faults found. When discussing issues found unit would turn itself off for no reason. Technician suspects infrared signal from other devices affecting this head unit. Two systems signed up for maintenance agreement.
Upon arrival checked motors, electrical components, and pressures. Cleared drain line and added Nubrite. Recommended UV bulb replacement and customer declined. Created estimate and emailed UV BULB REPLACEMENT TO CUSTOMER. DeltaT at. 21 degree split. Newer Turbo 200 recently installed. Renewed TAPS senior for customer. Left system in good operating condition.
Upon arrival system was not cooling, hot air was blowing from vents, checked refrigerant charge and found R22 system low on charge. Charged system to get them up and running, recommended a leak search, customer said they have already been quoted for a system we recommended being quoted for a new unit once again. Cleared drain lines. Left system in good working order.
Upon arrival system not operational technician found capacitor dead replace capacitor under warranty system is operational at this time. Recommend search protection at this home client to confirm with Office if she wants this.
15 Drop Duct System Tore out or duck system Moved supply grill in kitchen to be even with dining room living room area started to re-run ductwork will return Friday to continue on working Installed for Dr. system in the house cutting two brand new returns in both bedrooms and move supply Grill in kitchen started up system system running to factory spec customer satisfied paid in full
Uppon my arrival I found water inside the float switch. I cleared therein line and started the unit. I changed the filter and checked the coil. Coil is clean. Uppon further investigation found the dual capacitor extremely low. I got permission to replace with a turbo 200 5 year warranty capacitor. The air handler has a burnt out UV light ( it's the economy UV light). I asked if he wanted to replace but the customer politely declined at this time. I performed start up procedures and left the unit in good working condition. The customer signed up to our maintenance program so he could get the discounts. We need to schedule a tune up soon. I loaded my pictures and equipment information to service titan.
Install 1200 BTU air handler fan coil in master bedroom in new location per customers recommendation rand line height to existing stand for condenser on roof mounted new condenser Two existing stand modified existing stand to hold new mini split condenser perform pressure test in microns below 500 started up unit and performed all started procedures system running to factory spec instructed customer on usage of their new air-conditioning system collected payment change breaker customer satisfied also repaired drywall wall inside and repaired concrete wall outside
Install 3 ton 16 seer Bryant relocation brand new coffin box brand new supply and return plenums offset brand new 16 inch metal pipe for supply and return insulated and hung in garage ran a brand new three-quarter inch drain line installed brand new pad for condenser attached onto Copper attached on to terms that wire for relocation of air handler perform all started procedures including pressure test above 400 psi G vacuum below500 Âµm started up system and charge system to factory spec customer paid in full we will need to come out Monday to re-install a Wi-Fi Honeywell thermostat the thermostat we received out here is defective I temporarily installed a Honeywell T6 extra thermostat to get customer cooling customer satisfied with their new installation