Customer concerned about unit leaking water from unit plenum. Check blower motor operation and inspected evaporator coil condition. Checked drain pan and drain line, located clogged drain line. Cleaned vacuumed drain pan and drain line. Treat with solvent and prime drain line. Suggest new drain line in garage under cabinets to and thru front exterior wall to front planter. Pvc Drain pipe and hole thru concrete.
No cool System tripped hard lock out due to low refrigerant pressure. Refilled system and leak checked condenser. Found leak at low pressure sensor head. Office will call with repair quote and to set appointment for repair. Homeowner signed up for TAPS maintenance program. After repair is completed, we will complete the first maintenance for the year. System is cooling for now.
Upon arrival customer showed me an air handler in the closet that needed turned up. The evap coil is dirty and needs to be pulled and cleaned. Customer Denied work. Cleared the condensate with nitrogen and solvent. Checked the system for proper amps and voltage. Went to the condenser the check proper amps and voltage.
Attic Upon arrival customer showed me an ac unit in the attic that needed to be tuned. The evap coil is clean. Cleared condensate with nitrogen and solvent. Checked the system for proper amp and voltage. Went tot the condenser checked the system for proper amp and voltage. Found the 45/5 capacitor week. Replaced it with a Turbo 200. The contactor had a little burn marks and customer Denied. Also the compressor is over amping. I recommend a hard start and customer Denied. 19 degree delta T Mini split The evap coil is clean. Used shop vac to clear condensate drain. Checked the system for proper amp and volt. System is running at a 18 degree delta T.
Amana ASZ14 Pump 3 Ton. Install new air handler on new stand. New disconnect installed at air handler. New flex supply in closet. Install t6 pro thermostat. Breakers changed according to size. Condensor installed on pad block pad. Customer would like Bailey to email her a letter for her insurance company regarding the lightning damage that led to the unit needing to be replaced. Customer satisfied!
Upon arrival customer showed me the ac unit that need to be tuned up. The evap coil is clean. Clear the drain line with nitrogen and water. Checked all components for proper amp and voltage. Went to the condenser and checked for proper amp and voltage. Found a contactor with Pitt marks and a capacitor bad. Replaced the contactor and 35/5 capacitor with a turbo 200. We have a delta t of 18
Upon arrival customer showed me a ac unit that needed to be tuned up. Checked the evap coil and it was clean. Replaced customer supplied filter. blower is clean. Checked all amps and voltage. The UV bulb is burnt. Cleared the condensate with nitrogen and solvent. Check the condenser. All amps power and Freon level. Everything is working ass it should. Replace UV bulb under Warranty.
Upon arrival found system running and cooling. Inspected systems operations. System had a 21 degree delta-t and electrical components checked out. Left system in working order.
Upon arrival found pressures low, performed leak search. Found leak in condenser coil. We need to call to quote on the condenser coil. Once they have the price they might want Corey to come out and give and estimate on replacement due to cost. They wanted us to add refrigerant. Added 3 pounds of 410a refrigerant. Left system in working order.
Upon arrival found thermostat batteries in backwards. Switched batteries and tested operations. Left system in good working order.
Amana ASX16 AC 3 Ton. Install 3 ton air handler on new stand. Install uv light. New nest thermostat. Breakers changed to 35 amp. New condensor on new pad. Unit charged to subcool. Customer satisfied!
Technician went over system operations along with checking on electronics and refrigeration no faults found. When discussing issues found unit would turn itself off for no reason. Technician suspects infrared signal from other devices affecting this head unit. Two systems signed up for maintenance agreement.
Upon arrival checked motors, electrical components, and pressures. Cleared drain line and added Nubrite. Recommended UV bulb replacement and customer declined. Created estimate and emailed UV BULB REPLACEMENT TO CUSTOMER. DeltaT at. 21 degree split. Newer Turbo 200 recently installed. Renewed TAPS senior for customer. Left system in good operating condition.
Upon arrival system was not cooling, hot air was blowing from vents, checked refrigerant charge and found R22 system low on charge. Charged system to get them up and running, recommended a leak search, customer said they have already been quoted for a system we recommended being quoted for a new unit once again. Cleared drain lines. Left system in good working order.