Tom arrived, very quickly diagnosed and resolved the problem. Tom is a 10 on a 1-5 scale. The challenge was the error message indicated that a temperature sensor had failed and reality was the outside unit was without power. The other opportunity was called yesterday at 10:45 AM, was supposed to receive a callback that did not happen, called 3 hours later and the best they could do was a 12 PM appointment today.
Very good work, on time and at the quoted price!
I can not say enough positive things about my experience. The Price . Quality of information and service were amazing. Thank you
Raiko did an outstanding job checking out our (2) HVAC systems and was extremely knowledgeable and personable.
Total Air have been excellent from Rigo’s first visit to all contact with the office and guys on site
Arrived at customer's house for no cool. On arrival customer showed me to air handler unit. Condensate pipe had come loose from unit. Gave customer price to repair and customers agreed. Installed new male PVC fitting fitting and new section of condensate line. Sucked out drain line. Unit now running. Giving acceptable delta T. Told customers I am not extremely confident in female futting on drain pan.. appears to have been cross threaded in past. Collected payment and signature for today's work and left. Customers happy.
Install 2 ton 15 Seer mini split system air handler and Brand New hanging mounts modified supply and return plenums with mechanical fasteners and heat shield flush copper flush drain built and installed attic plywood decking for serviceability condenser on padlock pad fasten pads together and then fasten to the whole padlock pad to concrete system held pressure over 400 psi G and vacuum below 500 µm rewired existing nest thermostat changed breakers accordingly hung permit started system up and charged to factory spec walked customer through How to operate their brand new HVAC system customer paid balance in full via credit card job is complete and inspection ready
Arrived at customer's house for system inspection. On arrival customer showed me to air handler unit and laundry room. Check inside of unit and saw UV light that was not working. Toggled the breaker and the light would turn on but not stay emitted. Got light information in case customer would like to search for bulb. Suggested he go with our pure air. Row estimate. Next month upstairs to York unit and checked out that air handler. That air handler had bio growth and 2 UV lights that were not working. Next went downstairs to condenser's. 1st checked the York unit and your unit was getting cool but not Keeping up well enough. Customer also had complaints about unit. Suggested he get consultation and customer agreed. Next I checked the Bryant unit and the Bryant unit was fine. Unit was keeping up. All pressures and readings were of acceptable range. Talked with customer about options for installation as far as add as Adam's. Waited for Kyle to arrive. Signed customers backup with annua
Fan motor replacement Replaced fan motor and air handler. Started unit and unit now running fine. Collected payment and signature from customer. Customer happy.
System not cooling. I found the cause of this to be a bad blower fan motor in the evaporator. We will need to call in the morning to check warranty and order the motor for this unit. We will check pressures and system operation after repair has been made. All customer with price and timeframe of when we can get it.
Replaced defrost board in Rheem condenser unit. Changed out coil temp and ambient temp sensors provided with the board and recommended by manufacturer. Rewired common on the contactor back to the board (undo bypass). Home owner decided to change out weak capacitor while I was here today. Installed t200 capacitor with 5 year warranty. Cycled system to insure proper operation. Home owner paid for services today with a single check (#9797) for total balance. System operating properly at this time.
System not cooling. I found there to be two issues causing this. The first was that the contactor had failed so even when it got 24v it wouldnâ€™t pull in. The second issue is that the control board has a short on the common I have unhooked common and bypassed that part of the board allowing the unit to run for now but we will need to change this board out. The model and serial number is worn off from the unit so we have no way to order it now the customer said he thinks he has it somewhere in his paperwork and will find it and send it to us. The capacitor is also weak and needs to be replaced. The air handler has growth formed in it mainly on the blower wheel it should be cleaned. I did recommend considering replacement, for now we have decided to move forward with repairs. We will need to provide an estimate to change the capacitor as well as the control board on the condenser.
Upon arrival customer told me that the inside was working but the condenser will not kick on. Went to the condenser and checked the capacitor and it is good and also the contactor. Had 24 volts going to the board but not leaving to go to the contactor. Bypass the board so he customer has ac. Will need to order a defrost board.
On arrival found system low on refrigerant. Found a large amount of oil in vapor li e armor flex at air Handler. Leak is very small and could not pinpoint which weld is leaking. Home owner opted to refill today and leak search and/or repair in the future. Home owner requested I return for leak search. Left system cooling but still has small leak in refrigerant cycle.
Upon arrival customer told me the ac was not working. The thermostat said outside sensor not reading. I had no power going to the condenser. Customer just had a generator installed on Thursday. The problem has something to do with the generator and the extra box they put on the disconnect.
Replace two (2) UV bulbs. Returned to customers home to remove old UV bulbs and replaced them with new ones. Turned the thermostat down and made sure both unit are running and and working.
Cycled and inspected equipment. Found home not cooling properly and growth around vents caused by duct work leaking. Also found air handler cabinet contaminated with bio growth and filter impacted. Cleaned air handler cabinet and installed a new pure air x. Scheduled free estimate for duct replacement on Thursday 3-5 p.m. left system cooling for now. Recommend: new duct work and filter.
power board, noise filter p.c. board, electronic control p.c. board replacement Installed 3 new control boards. Cycled and inspected equipment. Left system in good working order.
Upon arrival checked electrical components, pressures, and drain line. Found a weak dual capacitor, customer decided to move forward on replacing the dual capacitor. Emailed customer. System was left in good working order.
Cycled and inspected equipment. Found power board, noise filter p.c. board, electronic control p.c. board failed. Left system off. Recommend: new control boards