Professional and hard workers
Very professional and polite
Maintenance 1 Completed maintenance on a strait cool split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Heat and cool working properly. Vaccuumed drain line. Found ptrap broken and laying on the ground at the co condensate drain exit. Rebuilt so drain will flow properly. Found wiring splice at the condenser heavily damaged and without insulation. Re wired from splice to the condenser. Found airhandler with heavy bio growth in the airhandler blower compartment. Discussed sanitizing and UV options with home owner. She declined at this time. An estimate will be.attached to this invoice. System operating normally at this time.
Maintenance Checked all electrical components for proper volts and amp draw. All components are within factory spec. Corrected loose common wire connection. Dual run capacitor tested 42.3 of required 45. This is still considered good. Cleared drain line. Changed out EAC filter for the homeowner. System pressures are at the correct levels. Cooling temps are normal. Replaced pure x uvc bulb that expires this month. Homeowner renewed maintenance membership today. System operating normally at this time.
No cool Found low voltage short caused by contactor. Replace the low voltage fuse and contactor. Tested system. System now cooling properly Homeowner signed up for maintenance program today.
Completed maintenance on a heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Back up heat tested ok. Cleared drain line. Found weak capacitor reading 20/1 of required 45/5. Replaced with a t200 cap with 5 year warranty. Found biogrowth in airhandler. Cleaned and sanitized the airhandler. Installed pure x uvc light system with lifetime equipment warranty and 3 year bulb replacement. Found low voltage wire insulation at condenser cracking. There is no bare wire showing. On the next maintenance this should be checked for any further deterioration. System is clean, sanitized, and operating properly at this time.
No heat Low voltage control signal not leaving the control board to energize the heat kit. Low voltage is ok from thermostat to the board. The board needs to be replaced. Unit is under warranty.
install tear out old air handler replace with new Ruud air handler tie an old copper low voltage high voltage dying plenum new thermostat tear out older condenser replace with new condenser on new pad thai down four corners Thai and high voltage low voltage and copper startup everything work in perfect condition test in heat and cool modes customer happy and paid
Tara all ductwork replaced with new plenum in return plenum new oxidizer on return plenum tie into the ballast for UV light in the plenum reroute copper and drain line for installation of new electronic filter
Upon arrival customer showed me an ac system in the garage that needed to be tuned up. The evap coil is dirty and will need a pull and clean. Cleared the condensate line with nitrogen, shop vac and solvent. Checked the system for proper amp and voltage. Went to the condenser and checked for proper amp and volts. The capacitor is in factory specs. Add a surge protector.
Performed maintenance on split system. Cleaned vacuumed drain pan and drain line. Adjust safety float switch and check operation. Check thermostat calibration and filter location. Inspected evaporator coil and blower motor operation. Cycled system in heat strip and inspected condenser coil. Check refrigerant levels and check test start up components. Unit is cooling well and drains at this time. Customer has 59.95 coupon. Customer is satisfied.
Completed maintenance on 3 split systems in the home. 2 newer systems are inverter / communicating, system 3 is traditional. Issues found: Drain pan on a/h 3 not installed correctly. No float switch on a/h Found capacitor on cond unit 3 weak 30 of 45 mfd Found growth in all 3 units airhandler. Homeowner purchased a 3 system maintenance program today. She has agreed to repairs and would like me to return 8am Wednesday morning ( 11/17/21 ). She will leave a check for balance that morning. Her handyman Howard will be at the home to let us in. We will need to build a quote for drain pan repair.
Trane unit #1 Upon arrival customer showed me and air handler in the garage that needed tuned up. Checked for proper amp and voltage. Cleared condensate line with nitrogen, vac and water. The evap coil is clean. The evap coil pan is rusted and falling apart. Went to the condenser and checked for proper amp and voltage. The contactor had some pitting to it and the capacitor was reading low. We also have a 14 degree split. Customer does donâ€™t want to throw money into a 25 year old system. Mention to customer we can come out tomorrow to give and estimate. She said she will call in the morning to schedule a time after she talks to her husband. Bryant unit #2 Upon arrival customer showed me a unit in the garage that needed to be tun d up. Checked for proper amp and voltage. The evap coil is clean. Cleared the drain with shop vac, nitrogen and water. Went to the outdoor condenser and checked for proper amp and voltage. The contactor is good. The 70/7.5 capacitor was reading low. Replaced
Upon arrival technician found capacitor had failed on compressor side, recommended replacement of capacitor client agreed. Technician measured refrigeration and sub cooling unit operating Within design parameters at this time.
Unit running upon arrival customer vaccumed out drain line. Owner said that itâ€™s an HOA issue so I did not perform any further drain clear out. If we get a call out again for drain issues we will have to clear it out and charge for it.
Customer ordered EAC pads. I am having them shipped directly to her home.
Performed routine maintenance on a ICP split system checked amps volts pressures coils caps drain line etc. replaced standard UV bulb. The system is running up to manufacturer specs. Customer is set for Friday 26th for estimate to replace upstarts system