1. Furnish and install two (2) capacitors. 2. Furnish and install one (1) contactor. 3. Perform start up procedures.
Upon arrival found system still frozen. Discussed options and they are aware of the age of the system so they would like to have Corey come out to give them a free estimate on replacing versus repairing. They would like a call in the morning to get that scheduled. System is off and fan set to on.
Upon arrival performed Evaporator Coil Clean in place. Cleared drain line. Installed a safety float switch tested to make sure the safety switch was operating correctly. Left system in good working order.
I performed a maintenance. I replaced the pitted/ burnt contactor. The evap coil is dirty, need to come back the chemical clean evap coil in place. I also noticed the air handler doesnâ€™t have a safety switch. This will prevent water draining out of air handler if drain line plugs up. I put quotes together..