1 time maintenance Completed maintenance on one of 2 systems in the home (upstairs 4 ton). Checked all electrical components for proper volts and amp draw. Both fan motors and compressors tested good. System pressures and temperatures are correct. Electric heat kit is working properly. Cleared drain line and added solvent to break up any debris. Air handler has very heavy biological growth. The system has an economy uv light and Reme halo system with expired bulbs. I discussed options for cleaning, replacing bulbs, and upgrading to a medical grade uvc light system. I have attached quotes to the invoice for these options. Home owner also wanted a quote to change out the float switches from a circuit style to a standard float switch. Due to age and condition of the system I also discussed replacing the system. The home owner just moved in and would like to wait to replace until a later date. Homeowner declined maintenance program at this time. System cooling at this time.
Complete evaluation of the duct system. After inspection I found the duct work compromised. All of the outer jackets have been torn away exposing the insulation inside the duct and the inner liner which the air travels through. Some ducts are kinked due to them being hung improperly. The ducts are also not sealed. This is a 7-8 drop system with a free air return. The attic is huge. No new supply plenum is needed as what is there is fine. I talked with Bailey and she said she will get with Kip to see if we can approve the job as we typically do not install duct work in the heat of the summer. The office will reach out first thing Friday morning to update the customer. If the install is approved we will need a comfort advisor to come out asap Friday to provide an estimate on the duct replacement. If the duct job is approved the service call fee will be credited back. All pictures are uploaded. Thank you for choosing Total Air!
Called out today due to no cooling. There are two systems in the home. The compressor on unit #1 is short cycling. Checked refrigerant pressures. System is low on R22 and compressor has been damaged due to the leak. Explained to client that in order to repair this machine you would have to perform a leak search, repair the leak and recharge the system. Even after the leak was repaired.. the compressor is still severely damage due to refrigerant loss. Client is selling the home and is not interested in replacing the system. He is aware that the cost of repairs will range from 2,500$ - 3,500+. System is 8 years past warranty and R 22 is no longer manufactured as of 2020. Left system off at disconnect. Thank you for always choosing Total Air!
Upon arrival customer told me the ac was shutting down and ON. I put gauges on and the and the high side was really high. I took an amp drawl and the compressor is over amping a lot. The compressor is going bad. All fan are working good. I recommend on replacing the unit do to age but also quoted out a compressor. There is no guarantee that there is anything else wrong with system. Customer wants to think about it and call us back.
Installed 2.5 ton rude split system air handler on brand new air handler stand with filter rack condenser on padlock pad foundation built up for flood zone change breakers accordingly 30 amp for air handler and 25 amp for condenser flush copper flush drain treated drains drain self-insuring drain was draining properly system held pressure over 400 psi G and vacuum below 500 µm released pressure and charged system to factory spec walked customer through on their brand new Honeywell T6 thermostat and ensure customer with fluid on operating their brand new HVAC system customer paid balance in full via credit card added 2 pounds of refrigerant to system to ensure proper chargeSystem is operating to factory spec we will need Joel to come on site to post a permit when we receive one besides that job is completed
Evap Coil replacement not under warranty, Replaced micro channel evaporator coil. Vaccuumed line set and adjusted charge. System did not need refrigerant added. Leak was very small and unit was slightly overfilled on last visit. Rebuilt drain line. Sealed filter rack door. Installed float switch on secondary drain outlet. Tested system. Pressures and Temps are correct. Condensate drain flowing better after rebuilding it properly. System operating normally at this time.
No cool Found system low on 410a refrigerant. Rechecked pressures after 10 minutes and pressures continued to drop indicating the system was freezing. Found oil in drain line indicating a leaking evaporator coil. System is a Frigidaire mixed coil system these systems are prone to evaporator coil leaks. Refilled the system for temporary cooling. Homeowner is aware that the system will continue to leak until replaced or repaired. I discussed repair versus replace on a 10 year old system with no warranty. He would like a quote for both so he can decide how he would like to move forward. Office to build repair quote and call to set an appointment for our comfort advisor to come by. System is cooling at this time. Model b6bmm036kb Sn. B6d130117270
Complete repairs to ac system. Remove old metal return duct that is crushed and not sealed properly. Replace with 14” flexible duct. Remove all insulation from coil and clean in place. Clear and flush the drain line. Left system in good working order.
No cool/ loud motor. Looked over entire 4 head mini split system. Between apt a and apt b. 3 of the 4 fan motors are making bearing noise while in operation. The blower motor in apt a bed room is exceptionally loud. 2 of the four heads have been cleaned but likely not fully. The other 2 have not been cleaned in some time. The condenser should be cleaned as well. There is debris starting to build up on the coil. The condenser coil can be cleaned during a normal maintenance at no extra charge. The indoor heads would need to be disassembled and thoroughly cleaned. This is a separate charge due to high amount of labor involved. Office will need to source motors and availability on 3 blower motors. Both in apt be and the kitchen unit in apt a. Office to contact owner with estimate for repair. I added quotes for maintenance program and for 4 mini split head cleanings. System cooling at this time.
Called out today due to ductwork being deattached. Upon arrival there were two large gaps in the return vents. Repositioned and taped gap shut. Used other pieces of loose duct work to try and make a seal at the bottoms. Client is aware that the coil is impacted due to the ductwork not being sealed. They are interested in investing in a UV light and applying the cleaning the same day. Clients are on scheduled to replace ductwork in November. Equipment is operating properly at this time. Thank you for always choosing Total Air
Was scheduled to go out to customers at 5 o'clock. GPS said I would not get there before 535. Saw customers know where they would not be available after 6. Called customer to see if it would still be OK for us to come and customer has chosen to reschedule for Thursday or Friday. Would like a call from the office to schedule time schedule time for service. Arrived at customer's house for System not cooling enough. On arrival customer showed me to air handler unit. Put thermal probe on supply and unit was creating excellent Delta T. Next looked inside the cabinet and the cabinet was clean. looked under evaporator coil and evaporator coil was also clean. Filters inside were clean. Next went to condenser unit And hooked up gauges. All pressures and readings are of acceptable range. Contact or sending proper voltage. Capacitor within acceptable range. Vacuumed out drain line. Unit is performing excellent. Went inside and got temperature readings from 3 warmest rooms. All rooms were prod
No cool Thermostat blank. Wires to thermostat are powered normally. Homeowner paid for a replacement honey well t6 wifi stat. I installed a non wifi Tstat for temporary cooling and heating. Home owner would like an appointment on thursday 11/18 if possible. Cycled system and is working properly now
Amana ASZ14 Heat Pump 3 Ton. Install air handler on new hanging kit. Install uv light. Change breakers according to size. Install t6 thermostat. New condensor on new pad. Customer satisfied!
Performed routine maintenance on older split system checked amps volts drain lines capacitors refrigerant pressure etc. system is starting to show its age would recommend system replacement in the near future. For now system is in good working order
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Recommended Service +: This includes the required repair to get your system running today and recommended service to items that I noticed also need some attention. I have also included solutions to extend the life of your system and protect it from future breakdowns. I am able to complete these tasks today at a discounted rate, shown below. Air handler inspection complete volts amps are within range ECM Tate motor. Coil bright and clear. Economy UV bulb has burnt out recommend replacement client has agreed. Technician does not have bulbs in stock on truck must return to install. Condenser inspection complete volts amps and microfarads within range contactor bright new capacitor recently installed. This unit is operating at this time no faults found. Must return with economy UV bulb to install. Tuneup complete.