Upon arrival customer had a audio of condenser short cycling. Cycled and inspected equipment. Found breaker for condenser tripped due to system short cycling. Reset breaker and found system operating in good working order. Customer declined membership at this time. Recommend: maintenance agreement 2 systems.
System down due to failed capacitor on compressor side, replaced under warranty this unit is now operational at this time. Technician recommended renewal of maintenance agreement due in October client wishes to wait closer to October to renew.
Completed member tune up #1. Cycled and inspected equipment. Found condenser coil dirty. Cleaned condenser coil. Left system in good working order.
Upon arrival checked motors, electrical components, and pressures. CUSTOMER SIGNED UP FOR TAP ANNUAL. Replaced UV bulb it was at 2 year limits. Had to use UV bulb from kit because had no bulb replacement for UV pure Air system. I will need 2 bulbs replenished (1 for kit n 1 for backup replacement). Cleared drain line and added Nubrite. Changed filter. Left system in good operating condition.
Customer was concerned about water setting in the drain pan. tested drain line by pouring water down pan and watching it flow out correctly vacuumed primary pan out system is running OK at this time
Technician cleaned evaporator coil and disinfected. The service is completed.
Completed tuneup. This unit is operational but capacitor has lost beyond 10% of its microfarads recommend replacement. Fan motor is two times the amp draw it should be. Fan side of capacitor is fine suspect slow degradation or performance in fan recommend replacement in the future. Recommended Repairs: This includes the minimum required repair to get your system running today and recommended service items that I noticed also need attention. I am able to complete these tasks today at a discounted rate, shown below.
Upon arrival found short in air handler. Had to do a wire repair in 2 places. We are aware of the age of the system and she would like for Corey to come out due to the over current from the age of the system. We need to call and schedule that. Left system in working order.
Completed system tune up on both systems. Checked pressures, volts, amps and all electrical components. Checked evaporator coils. Cleared drain lines. Found system #2 was 2 lbs low on r410a. Added 2lbs r410a and also added 1 tube of easy seal to try and stop leak. Lefr system in good working order.
Upon arrival performed maintenance. Inspected all the systemâ€™s electrical components, coils, pressures, and filters. Cleared drain lines. The upstairs unit is not cooling because of the leaking refrigerant. He is going to reach out to us when he is ready to move forward on replacement, the system is NOT cooling. System number 1 had a failed dual run capacitor and needed a wire repair, we moved forward on these issues. Recommended on installing 3 surge protectors (1 per unit) emailed quote. Left 2 systems in good working order.
Uppon my arrival I found the compressor running but OD fan motor not. The condenser control board had failed and dropped one leg of power going to the motor. I bypassed the board and got the fan to come on. DeSean was present and said he would be the one replacing the board. I let the unit run and checked the amp draw of both motors. The amp draw is good and unit is cooling now. I charged the customer for service call fee and left the unit in good working condition.
System #3: I had to reset the thermostat a few times and fix some low voltage connections. Sean came. I checked pressures, he added 410 a refrigerant to the system with his own can. I found I dirty 20â€x20â€x1â€ filters which needs to be replaced. Sean does all the maintenance for the properties.
Completed system tune up. Checked pressures, volts, amps and all electrical components. System in very poor condition. System needs blower run capacitor, condenser dual run capacitor. And condenser contactor. System also running high head pressure. System replacement highly recommended.
Installed Turbo 200 Dual Run capacitor in CU and performed start up procedures. Unit is in good running condition.
Upon arrival we found 2nd floor system off on float. Got approval to clear drain. Cleaned drain line with cleaner and nitrogen. Finally got line clear. Inspected operations. Left systems in working order.