We got our 2 A/C Units replace in one day. That is a spectacular feat. They took our old ugly dirty units air handler and roof top compressor units and put in 2 new beautiful units quickly. They were very organized and came on time and even were finished early. They organized a crane company to show up when they needed to hoist the new units up and remove the old off the roof. They also put carpet and hardwood protection down so there was not harm or dirty floors left behind. Very satisfied and it was money well spent.
First of all the office staff is a breath of Total FRESH Air”…lol. No, but seriously they were calling to update me on the time the tech would arrive & they were SO nice! Then the tech came & thoroughly checked everything. He explained everything along the way & left me with tips on how to keep up my AC unit. The presentation was very excellent.
Called out today to perform a precision tune up on four units. Checked all electronics and motor components to ensure equipment is operating within manufacture specifications. Checked and replaced all filters and cleared drain lines. Measured the temperature drop and rise across the coils. The farthest unit in the air handler emergency drain pan is completely rusted out. Made client aware of its condition and the fact that it could deep through onto the ceiling. The guest house UV bulb is out and the coil is rusting and condensation into the drain line. Outside I removed the fans from the condensers and cleaned the coils. I noticed that the contactors were heavily pitted outside. Armaflex is rotted and falling off of both carrier condenser units. Replaced three contactors, Armaflex, and renewed maintenance agreement. Equipment is operating properly at this time. Thank you for always choosing Total Air
Called out today due to no cooling. Tenants told me that this has been going on for about a week now. Upon arrival float switch was tripped due to the ice thawing. Left system off with the fan on to help the ice melt. The filter was extremely dirty and the ice was stuck to it. I was unable to see the under side of the evaporator coil. Thank you for always choosing Total Air! Wade h 11/10/2022 Unit has thawed out. Checked thermostat calibration and filter location. Filter is very dirty and needs to replaced. 18x18x1 Highly recommended pull and clean the evaporator coil. The coil is extremely dirty and can not breathe properly. Unit will freeze up when coil is not cleaned and can not pass air. I have sent this customer recommended estimate for membership and pull and clean evaporator coil. Needs Customer approval for evaporator cleaning.
Replaced blower motor and wheel. Tested system operation. Equipment is operating properly at this time. Thank you for always choosing Total Air!
Upon arrival customer showed me a water stain on the sheet rock in the garage. I went up in the attic and there is no drain or or water in that area. I want to say it is coming from the roof.
No cool. Downstairs unit drain line backed up. Drain lines are all built up with debris. I cleared the drain with pressure at no charge today. Home owner authorized drain solve treatment on all four main house drains. Due to weather and lack of supplies this will have to be scheduled next week. Home owner wants to purchase 4 oxidizers to add to her existing pure air system. I do not have a stand alone task for this so we will have to give estimate Tuesday morning. System cooling at this time.
Tune up/ check system. 3 ton unit less then 2 years old. Not keeping temperature and will not reach set point during the day. System has multiple issues 1. Return duct is undersized and causing unit to sweat heavily. The previous company tried to add a second return grill and duct in line with the original return. This has a highly diminished effect on the amount of the the system is pulling. This needs to be corrected to allow system to breath properly and stop sweating. 2. Split temp (delta) at airhandler plenum is 16 degrees. While this is lower then the desired split, this should be enough to satisfy the temperature. When reading Temps at the registers, the air has gained 4 to 5 degrees and now has a delta of 12. This will not reach a set point of 72 in the home. The supply duct work is picking up heat load before being delivered to the living space. Supply Ductwork should be replaced. 3 pressures seem marginally low for a Rheem system. Due to the air flow issues, this may
Called out today to perform a precision tune up. Checked all indoor and outdoor electronics and motor components to ensure equipment is operating within manufacture specifications. Checked filter and cleared drain line. The coil is heavily impacted with biological growth. It’s coating the wires, blower wheel and casing. I highly recommend cleaning or permanently eliminate growth by UV sterilization. Outside I ensured the community drain was free of blockage. On the condenser I noticed that the contactor coil is becoming pitted as shown in video. The bottom of the condenser coil is extremely corroded as well as the shell of the compressor. Client choose to get a one time cleaning of the blower wheel and the evaporator coil in place. Also replaced contactor. Equipment is operating properly at this time. Thank you for always choosing Total Air! Clean and go
Terror out existing rooftop condenser fly off with crane flying new one with crane I brought it up fly 70 gallons of roof paint to the top of roof with crane hair out air handler on stand coffin box replace call tin box replace air handler Cayenne high voltage low voltage drain line copper Thai in coffin box put in new surge protector at disconnect on roof will need to return to put in Elite light on both units nitrogen test 400 PSI vacuum down to 500 Micron start up everything working in perfect condition
Customer concerned about unit not cooling properly. Checked breaker and safety float switch and inspected drain line. Checked thermostat calibration and filter location. Customer replaced filter. Unit is cooling well and drains at this time. Customer approved for 1/2 preventative maintenance visit and (2) uv bulb replacement Performed preventative maintenance tune up. Checked blower motor operation and inspected evaporator coil condition. Checked safety float switch and inspected drain line. Cleaned vacuumed drain pan and drain line. Checked thermostat calibration and filter location. Customer replaced filter at this time. Checked condenser operation and rinse condenser coil. Checked refrigerant levels and check test start up components. Replace (2) 24 volt uv light stick probe to prevent biological growth in air handler and evaporator coil.
Customer concerned about unit not cooling properly. Thermostat given error code. Checked thermostat calibration and filter location. Checked thermostat wiring and air handler control board. Checked low voltage wiring in condenser. Unit installed by another company. Customer is not satisfied with that company. Bad low voltage wiring, needs to be replaced with 18/4 stranded wire that is designed for communication and plenum rated. Follow up to be replaced and repaired. Needs 50â€™ communication wire and 2-3hrs. Also discuss new membership and units to be performed preventative maintenance. 2/18/2022. Replace old thermostat wire with new 4/18 stranded communication wire. Termite all connections and checked operation. Set up WiFi for customer and checked unit operation. Unit setup and cooling at this time.
Completed maintenance on a heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Dual capacitor tested ok. Heat kit tested ok. Changed supplied filter. Split temp above 19 degrees. Found biogrowth in airhandler. Cleaned and sanitized airhandler cabinet. Pulled blower assembly and treated. Installed a pure x uvc light system with life time equipment warranty. The pure x has a 3 year bulb life. Re assembled and tested . System clean and operating normally at this time.
Installed filter rack and EAC system. Sealed plenum and rack. Tested EAC system. System working properly. Left box of filter media on air Handler for easy replacement.
Performed preventative maintenance on the system. Cleaned drain, checked filter, cleaned return grille, checked coils, tested/inspected electrical components, checked refrigerant pressures, tested reversing valve operation, and tested operation of the system as a whole in both heating and cooling modes. I found that the run capacitor in the condenser was weak. Customer gave approval to change this out. He also has signed up for the TAPS Annual Membership. I ensure the system was operating after repairs. This system has 8 degrees subcool with a 19 degree TD.
Maintenance 1 Performed maintenance on a Rheem heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. System refrigerant pressures are at the correct levels. Cleared the drain line. Home owner signed up for our maintenance plan. He also requested a UV system. I installed a pure x iv system. He would also like a EAC filter system installed. For EAC filter install, we will need a filter rack from Rheem. The rack will need to be installed between the return and return plenum of the air Handler. Office will contact home owner with a quote for this. Home owner would also like a quote on a mini split addition. Corey is scheduled for a visit between 10 and 12 tomorrow. System operating great at this time.
Arrived at customers house for system inspection. On arrival customer show me to to Erin Angel is. Started on air handler on the second floor. Air handler was putting out proper delta-t. Had a bit of covering on the underside. Install put filter on rack instead of on unit. Suggested customer get an electronic filter for the proper filter place. All electric wiring was secured. Next went to upstairs air handler. Inspected evaporator coil and saw some bio growth beginning to form. Fan in electrical cabinet were clean. Unit was putting out proper delta-t. Next one to condenser units. Both units pressures and readings were of acceptable range. Both units contractors were putting out proper voltage. Capacitors with an acceptable range. All units check out. Gave report to customer and customer was please. Collected payments and signature and left. Customer happy.