We got our 2 A/C Units replace in one day. That is a spectacular feat. They took our old ugly dirty units air handler and roof top compressor units and put in 2 new beautiful units quickly. They were very organized and came on time and even were finished early. They organized a crane company to show up when they needed to hoist the new units up and remove the old off the roof. They also put carpet and hardwood protection down so there was not harm or dirty floors left behind. Very satisfied and it was money well spent.
First of all the office staff is a breath of Total FRESH Air”…lol. No, but seriously they were calling to update me on the time the tech would arrive & they were SO nice! Then the tech came & thoroughly checked everything. He explained everything along the way & left me with tips on how to keep up my AC unit. The presentation was very excellent.
Terror out existing rooftop condenser fly off with crane flying new one with crane I brought it up fly 70 gallons of roof paint to the top of roof with crane hair out air handler on stand coffin box replace call tin box replace air handler Cayenne high voltage low voltage drain line copper Thai in coffin box put in new surge protector at disconnect on roof will need to return to put in Elite light on both units nitrogen test 400 PSI vacuum down to 500 Micron start up everything working in perfect condition
Customer concerned about unit not cooling properly. Checked breaker and safety float switch and inspected drain line. Checked thermostat calibration and filter location. Customer replaced filter. Unit is cooling well and drains at this time. Customer approved for 1/2 preventative maintenance visit and (2) uv bulb replacement Performed preventative maintenance tune up. Checked blower motor operation and inspected evaporator coil condition. Checked safety float switch and inspected drain line. Cleaned vacuumed drain pan and drain line. Checked thermostat calibration and filter location. Customer replaced filter at this time. Checked condenser operation and rinse condenser coil. Checked refrigerant levels and check test start up components. Replace (2) 24 volt uv light stick probe to prevent biological growth in air handler and evaporator coil.
Customer concerned about unit not cooling properly. Thermostat given error code. Checked thermostat calibration and filter location. Checked thermostat wiring and air handler control board. Checked low voltage wiring in condenser. Unit installed by another company. Customer is not satisfied with that company. Bad low voltage wiring, needs to be replaced with 18/4 stranded wire that is designed for communication and plenum rated. Follow up to be replaced and repaired. Needs 50â€™ communication wire and 2-3hrs. Also discuss new membership and units to be performed preventative maintenance. 2/18/2022. Replace old thermostat wire with new 4/18 stranded communication wire. Termite all connections and checked operation. Set up WiFi for customer and checked unit operation. Unit setup and cooling at this time.
Completed maintenance on a heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Dual capacitor tested ok. Heat kit tested ok. Changed supplied filter. Split temp above 19 degrees. Found biogrowth in airhandler. Cleaned and sanitized airhandler cabinet. Pulled blower assembly and treated. Installed a pure x uvc light system with life time equipment warranty. The pure x has a 3 year bulb life. Re assembled and tested . System clean and operating normally at this time.
Installed filter rack and EAC system. Sealed plenum and rack. Tested EAC system. System working properly. Left box of filter media on air Handler for easy replacement.
Performed preventative maintenance on the system. Cleaned drain, checked filter, cleaned return grille, checked coils, tested/inspected electrical components, checked refrigerant pressures, tested reversing valve operation, and tested operation of the system as a whole in both heating and cooling modes. I found that the run capacitor in the condenser was weak. Customer gave approval to change this out. He also has signed up for the TAPS Annual Membership. I ensure the system was operating after repairs. This system has 8 degrees subcool with a 19 degree TD.
Maintenance 1 Performed maintenance on a Rheem heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. System refrigerant pressures are at the correct levels. Cleared the drain line. Home owner signed up for our maintenance plan. He also requested a UV system. I installed a pure x iv system. He would also like a EAC filter system installed. For EAC filter install, we will need a filter rack from Rheem. The rack will need to be installed between the return and return plenum of the air Handler. Office will contact home owner with a quote for this. Home owner would also like a quote on a mini split addition. Corey is scheduled for a visit between 10 and 12 tomorrow. System operating great at this time.
Arrived at customers house for system inspection. On arrival customer show me to to Erin Angel is. Started on air handler on the second floor. Air handler was putting out proper delta-t. Had a bit of covering on the underside. Install put filter on rack instead of on unit. Suggested customer get an electronic filter for the proper filter place. All electric wiring was secured. Next went to upstairs air handler. Inspected evaporator coil and saw some bio growth beginning to form. Fan in electrical cabinet were clean. Unit was putting out proper delta-t. Next one to condenser units. Both units pressures and readings were of acceptable range. Both units contractors were putting out proper voltage. Capacitors with an acceptable range. All units check out. Gave report to customer and customer was please. Collected payments and signature and left. Customer happy.
No cool: On arrival, I found capacitor and headstart inoperable. Common high volt wire was burnt off as well. Replaced contactor and rebuilt wiring. System now cooling normally.
Found not cooling due to clogged drain line. Cleared with high pressure nitrogen. Primed drain. Checked operation. System cooling and draining properly at this time.
Install air handler on new hanging kit. Install uv light. Install t6 pro thermostat. Electrician on site to change breakers correctly and add electrical. Install condensor on new pad. No permit was posted. Inspection form needs to be completed. Customer satisfied !
Cycled and inspected equipment. Found transformer failed, air handler control board failed, blower motor failed, run capacitor weak, dual capacitor weak, contactor pitted, air handler cabinet and immediate duct work contaminated with bio growth. Customer declined repair quote since equipment is dated from 2001. Customer requested a free quote to replace equipment. Scheduled Corey today 12-2. Left system in same condition. Recommend: new equipment due to cost of repair, age, and overall condition of equipment.
Upon arrival customer had a audio of condenser short cycling. Cycled and inspected equipment. Found breaker for condenser tripped due to system short cycling. Reset breaker and found system operating in good working order. Customer declined membership at this time. Recommend: maintenance agreement 2 systems.
System down due to failed capacitor on compressor side, replaced under warranty this unit is now operational at this time. Technician recommended renewal of maintenance agreement due in October client wishes to wait closer to October to renew.
Completed member tune up #1. Cycled and inspected equipment. Found condenser coil dirty. Cleaned condenser coil. Left system in good working order.