Customer has three systems with three-quarter inch drain line teeing into a 1 inch drain line. The entire drain system was clogged up at the 90 elbow outside next to the unit. I cleared out the entire drain line system and now all three drain lines are draining properly.
Upon arrival to scheduled multi system maintenance (4) I was shown to 3 A/H units located in the attic above the master bedroom closet. Immediately pulled off panel doors to inspect all electrical components connections, collect amp draw/voltage readings off equipment, and check the evap coil for cleanliness. Evaporator coils were clean, but significantly rusted. This could possibly be an issue down the road. All electrical components connections were secure and all amp draw/voltage readings were all within range of factory specifications. Collected temperature readings and had a 17-21 degree delta T temperature split in cooling on all 3 systems. Changed filters at the unit. All of these A/H units are equipped with Pure Air X UV light systems that are all fully functional at this time. There are separate air purification systems that were installed back in 2015 which are not in operating condition at this time. I do suggest having these replaced to ensure no loss of indoor air qu
Arrived at customer's house to apply drain solve to 3 units and change a contactor. On arrival turned off unit 1 and changed contactor. Turned unit back on and unit is running fine. Next located air handler units and applied drainsolve to all 3 lines that go down to a 1" common drain And then reduce to a 3/4 outlet. Applied drainsolve and ran hot water behind each drain line. Vacuumed drain line from 3/4 outlet and got a lot of drain debris. Although the Liquid line filter dryer did have Rust on it customer decided to not take preventative action and get filter dryer changed out. All units now running fine. Checked in with customer and customer is happy with work performed. Collected payment and signature and left. Customer happy.
Called out today to replace outdoor board. Turned both systems off and after the delay the system kicked on. Client is aware that it will take hours to cool. Client told me that her house just got hit with lightning yesterday and I told her to keep a close eye on her systems and to call if she has any issues. Thank you for always choosing Total Air!
Complete warranty blower motor replacement. Cycle and inspect equipment. Unit is in normal operating condition.
Unit #1 Upon arrival customer showed me an ac unit in the attic that needed tuned up. The evap coil is clean. There is microbial growth in air handler installed a pure air x and whipped down the air handler. Cleaned the condensate pump with water and nitrogen. Checked the system for proper amps and volts. Went to the condenser and sprayed of the condenser coil with water. Checked the system for proper amps and volts. Found a week capacitor and installed a turbo 200 Unit #2 Upon arrival customer showed me an ac unit in the attic that needed tuned up. The evap coil is clean. There is microbial growth in air handler installed a pure air x and whipped down the air handler. Cleaned the condensate pump with water and nitrogen. Checked the system for proper amps and volts. Went to the condenser and sprayed of the condenser coil with water. Checked the system for proper amps and volts. Found a week capacitor and installed a turbo 200 Unit #3 Upon arrival customer showed me an ac unit in the
Customer met me in the drive way and said she has dinner plans with her grand children and does not want to deal with it tonight. She want service tomorrow
Returned to customers home to perform leak search. The unit is completely empty. I put nitrogen in the system to perform leak search. I hear the leak and it is coming from under the home. Can not pin point the leak.
Upon arrival performed maintenance on all 4 systems, inspected electrical components, pressures, coils and drain lines. Replaced all filters for the 4 systems. UV lights and surge protectors working properly. Left systems in working order.
Air Knight UV replacement cell Installed 3UV\ionizer systems. Please note one unit retention bolt had to be sheared off due to detachment and spinning free could not remove module without informed homeowner and taped unit up no faults other than this these units are operational at this time
Upon arrival performed maintenance on 4 systems. Cycled in heat and cool mode. Inspected systems electrical components, coils, pressures, changed filters, and cleared drain lines. The 3 units upstairs have us lights and the bulbs are burnt out. Mentioned this issue and we need to get a quote and send over how much it would be to replace the bulbs. All 4 surge protectors are working. Left system in good working order.
Upon arrival found that the compressor for system 1 had over heated and opened the internal safety. I inspected all electrical components and cooled down the compressor. Performed starry up and noticed that the system was going into a vacuum. After further testing and verifying with Jason we concluded to replace the TXV. Called Totaline, TXV info on pinned notes. Materials: 8 lbs R410A. TXV Recovery machine and tank. Extra nitrogen( Refrigerant circuit must be flushed properly). 1 tech 4 or more hours labor.
Performed system tune up in 4 split systems. Inspected all electrical components and found no issues. Capacitors are in range. Coils are clean. UV systems are not operational and I highly recommend replacing the expired bulbs to improve air quality. I provided info to the office on my last visit to acquire them. Please Contact customer with pricing on replacing the cores 20 minutes per unit labor, 4 units. Flushed all drains with nitrogen. Left all systems in good working order. Note: please contact costumer next week for TAPS renewal.