Complete member precision tune up. Inspect all electrical components and ensure proper amperages and voltages. Clear out drain line using nitrogen. Evaporator coil picture uploaded to ST. Fan capacitor was low and customer agreed to change out to the mini turbo 200. Delta t split was 21 degrees. Condenser motor and compressor amperages look good a turbo cap was installed last year. Contactor is in good condition. Offered pure air x light and media cleaner to customer. He will get back to us in the next week and is very interested. Media filter would be 16x20x1. Customer satisfied!