Upon arrival condenser operational air handler was not. Tech tested tstats (nest and Honeywell), no faults. Tech tested Honeywell zone control. Zone control passing only 14v. Tech deenergized zone control panel and reenergized. Zone control panel reset and operated correctly. As this is an internal intermittent fault occurring in zone control recommend replacement. Informed client, client requesting pricing. Office to follow up with pricing and availability. Unit is operational at this time.
Completed system tune up on all systems. Checked pressures, volts, amps and all electrical components. Checked evaporator coil. Cleared drain lines. Replaced burnt contactor in system #2. Reached all air filters in home. Left systems in good working order.
Upon arrival found system leaking water. On inspection found area of concern and made a minor repair. On further inspection found that the system was low on refrigerant. Added 2 pounds of 410a refrigerant. Also recommended on replacing the weak dual run capacitor. We moved forward with all repairs. Cleared drain line and drain pan. Cleaned up as much water as possible around the air handler. Recommended on placing a fan in the return to dry up some of the wood. Left system in good working order.