Completed maintenance on 3 split systems in the home. 2 newer systems are inverter / communicating, system 3 is traditional. Issues found: Drain pan on a/h 3 not installed correctly. No float switch on a/h Found capacitor on cond unit 3 weak 30 of 45 mfd Found growth in all 3 units airhandler. Homeowner purchased a 3 system maintenance program today. She has agreed to repairs and would like me to return 8am Wednesday morning ( 11/17/21 ). She will leave a check for balance that morning. Her handyman Howard will be at the home to let us in. We will need to build a quote for drain pan repair.