Upon arrival checked motors, electrical components, and pressures. Cleared drain line and added Nubrite. DeltaT at 16 degree split and caution on possible slow leak. Pressures seem fine and no visible oil at CU. Indoor AU closet coil in good shape and no visible leaks Indoor blower cap replaced and motor still overamping but dropped considerably after mini turbo installed. Also changed outdoor CU capacitor due to high fan capacitance over limits. Customer will call office in fall after returning from Conneticut as he lives here half the year. Left system in good operating condition.