Upon arrival customer showed me an air handler in the attic that needed turned up. The evap coil is clean. Cleared the condensate with nitrogen and solvent. Found a lot of microbial growth build up in the system. Recommend a pure air X and customer Denied. Checked the system for proper amps and voltage. Found the 10 run capacitor bad and replaced with a mini turbo. Went to the condenser the check proper amps and voltage. Found the contactor pitting replaced the contactor. Found the 40/5 Capacitor under factory specs and replaced with a turbo 200. Also a run capacitor below factory spec out at the condenser and replaced with a mini turbo.