Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Customer stated upon arrival system experienced a brown out and compressor wasn't running. Just prior to arrival system turned back on. Suspect compressor shut off on internal over load. Compressor amps are slightly above normal but within factory specifications. Left system in good working order.
I found the dual shaft blower motor failed(oil leaks), the blower relay on circuit board failed and the contractor is pitted/ burnt. The evap coil is impacted with growth. The Bard system has wear and tear due to age (2004). Due to the age and high repair cost, I recommend on replacing the system. We discussed on putting in a two head mini split system. We are a Mitsubishi diamond dealer which we offer 12/12 year warranty on parts and compressor. Bryan our comfort advisor will be coming out tomorrow between 9am-11am.