Techs were on time, and kept us informed about there progress.
The technician arrived on time for the scheduled appointment. He was very friendly and allowed me to make several calls to answer the questions that he had.
The man was so helpful during his time here. Kept us well informed.
cory/5am Kitchen Suppression Inspection ***NEW CUSTOMER 3/2017*** Semi-Annual Inspection Kitchen Equip Desc: Inspect (1) Ansul 9 Gal. Inoperable Deficiency for Ansul R102 9 gallon Main hood: Ansul 9 gallon **Detection line failed due to excessive grease buildup under hood** Parts needed: **8 detectors** **7 corner pulleys** **60ft of conduit** **60ft link-line cable** **5-6 hours labor** Hood sizes: #1 10ftx4ft #2 5ftx4ft #3 10ftx4ft #4 40inx37in Duct sizes: #1 21inx10in #2 10inx10in #3 21inx10in #4 10inx10in
Onsite to troubleshoot OSYSU tamper. Found bad module and address corrupt on system. Replaced module and adjusted module address. Devices function properly. System normal at the time of departure.
Portable Extinguishers Inspection