very nice guy doing hes job.
Great very helpful with the Question
They very nice guys and they are doing very good job. Thank you guys.
Very nice GUYS trying best.
Guys was very carefully to explain to me what is the problems etc
James was professional and informative. He inspected my sprinkler heads for leaks and/or possible replacement. Right now I am waiting on an estimate for repair and/or replacement so this review is for James and the inspection only, at this point.
Kitchen Suppression Inspection
11/12 1130-12p see shandode Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (2) SAFETY CHEF Alarm Int: No Inoperable Deficiency for Safety Chef PPA27-W 2.5lb Top floor main kitchen: Safety chef 1 &2 System due for hydro testing Last hydro test was performed in 2008 **cylinder lost pressure and needs to be recharged** No alarm or bell interlocked to fire suppression
Kitchen Suppression Repair
PAUL 301-980-4857 7a DO NOT DROP! Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) GUARDIAN 21ST. CENTURY Alarm Int: Yes