Lee has been out on two services here and both he took his time to explain and question that I had. Great Work! Thanks
steve8-12/see steve Kitchen Suppression Inspection Ansul R-102 1.5 Gallon: Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 1.5 GAL Alarm Int: Yes Inoperable Deficiency for Ansul R-102 1.5 Gallon: Customer added new equipment under hood, appliances lack protection. System is currently Ansul 1.5 gallon and may need to be upgraded to a 3 gallon system. Quarter inch pipe needs to be replaced when system is upgraded.
jerry 2-230p Kitchen Suppression Inspection Ansul R102 3 Gallon: Semi-Annual Kitchen Suppression Inspection Equip Desc: (1) Ansul 3 Gallon System