Chicago was on time, and kept me updated as to what was going on.
Technician failed to protect an expensive kitchen equipment while working on top of it. Tools were set up in the table where the chef prepare the food.
You all had two great guys here to do a task , that was done and completed to our satisfaction.
Duane is an asset to your team. Great representative for your company.
Technician made no contact with Management or Maintenance Team. We only knew he had been to the office because we got a summary email.
The technician was courteous and very professional.
Great service, relatively easy and very communicative.
Great job ! Quick and ease
I have been using guardian fire protection for years to service the condominium association I manage in DC. They have always been on time, pleasant and competitively priced.
Portable Extinguishers Inspection
IF HOOD IS NOT UL COMPLIANT, DO NOT DO INSPECTION. CONTACT BRAD IN THE GUARDIAN OFFICE Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Inspection Equip Desc: Kitchen System(s) Annual Extinguisher Inspection Equip Desc: Extinguishers Deficiency for 6 lit K Class Kitchen: Kclass extinguisher needs to be installed inside kitchen area** 5lb abc extinguisher needs to be installed (Dishwasher area) **5lb abc extinguisher needs to be installed on the left side of building behind the register** 10lb abc extinguisher needs to be installed (Basement storage area) bottom stairway 10lb abc needs to be installed (Basement exit)
05/09 Sch w Michael 1PM ONLY Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 3 GAL Alarm Int: Yes Inoperable Deficiency for Ansul R-102 3G Kitchen next to hood: Exhaust fan failed to activate when system was tested **Exhaust fan needs to be interlocked to fire suppression system**
martin 830a call Rueben when you arrive (C) 202-345-4102 Kitchen Suppression Inspection Semi-Annual Inspection Kitchen Equip Desc: Inspect (1) Ansul 9 Gallon System Suggested for Ansul R-102 9 Gallon Kitchen: Access panels to duct detectors have vary sharp edges (Dangerous) Inoperable Deficiency for Ansul R-102 9 Gallon Kitchen: Ansul 9 gallon: Water wash system failed