Cycled and inspected equipment. Found condenser fan motor failed, dual capacitor weak, contactor pitted, and compressor drawing high amps. Condenser name plate has worn completely off and unit is dated from 1995. Customer requested quote to replace. Scheduled quote for today. Left system in same condition. Recommend: new equipment due to cost of repair, age, and overall condition of equipment.