The guy was very professional and well mannered.
Sch. w/ Pong 10-11 am F/A set with Victoria on 7/09 Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen Inspection Equip Desc: (1) Protex L4600 Kitchen Suppression System Annual Extinguisher Inspection Equip Desc: (2) Extinguisher(s) Inoperable Deficiency: Detection line failed to activate due to excessive grease buildup under hood 6 detectors 3 sticks of conduit 1 corner pulley 30ft steel cable 2-3 hours labor Inoperable Deficiency: Extinguishers: Lacks protection in kitchen (No kclass extinguisher) New kclass extinguisher needs to be installed Front dining area lacks protection (No 5lb extinguisher) New 5lb abc extinguisher needs to be installed behind register Suggested: Hood sketch
Portable Extinguishers Inspection
theresa/2-4 Annual Inspection Extinguisher Equip Desc: Inspect (2-3) Extings Portable Extinguishers Inspection
Emergency / Exit Lights Repair