I performed a summertime tune up on a tappan heat pump in perry.
I performed a Silver level visit tune up on the equipment. Testing system operations, component amperages, capacitor ratings, cleared the drain line, checked the filter, cleaned the condenser outside, and checked the thermostat. The system is working properly at this time. Thank you for your business today. Perry, Florida.
Today we performed a commercial winter tune up on your Daikin heat pump mini split unit, everything is working properly at this time. Thank you for your business. Perry Fl
Performed commercial maintenance as agreed. Cleared drain line and washed filters. Sprayed coils on outside unit and cleaned them. Tested and amped unit. Unit is operating properly at this time.
Preformed Silver Level maintenance 1st visit on one heat pump system. I checked all parts and operations in heat mode. The (1) 20x25x1 filter was good and the drain line was cleared. The customer was emailed a copy of the maintenance report. Overall the system is heating properly at this time.
Performed a maintenance on a Tappan air conditioner in Perry FL
Completed Maintenance On Tappan Unit