Always completes work in a professional manner
Response from PDM Plumbing, Heating, Cooling Since 1885:
“We aim above the mark to hit the mark.” — Ralph Waldo Emerson. Thanks Chuck for your review and for trusting in PDM Plumbing, Heating, Cooling Since 1885! We look forward to our next maintenance visit. Stay well.
A cracked coupler caused a lot of water damage, but you could not have been more responsive. Thank you for the quick and professional service!
Backup generator maintenance. Inspected and serviced generator, Inspected and serviced furnace for season, serviced humidifier and replaced filter media panel. Sump pump inspected, pumps are 7 yr old.
Service 2 A/C system, replaced customer supplied filters, replaced battery for backup battery. Please see Jake for pricing.
Clean and check to furnace system is under plan. This is the second visit on this service agreement. Replaced two #35 humidifier pads. Resealed collection cover on front of furnace. Checked air filters, both okay at this time. Bad vibration on second floor furnace, need to return and replace blower wheel and motor. Parts under warranty, not labor. See photo. 11-15-22 replaced second floor blower motor and wheel, bad vibration (parts under warranty). Delivered 2- Air Baer 20x25x5 media filters (inventory). Inspected first floor furnace for issues (no heat). Found vacuum hose disconnected, reconnected and tested. To be billed. Materials on P.O.
Service furnace and humidifier
Service A/C for season, install new WI-FI for backup generator.
Clean and check to air conditioning systems. Renewed customer service agreement for both systems. This is the first visit on this new plan. Need two filters for furnace cleaning. 20x25x4 Trion. To be billed.
Cleaned and checked furnace for the season.
Service generator, replaced 2 Honeywell prefilters on electric air cleaner. Service furnace and humidifier for season.
Installed water flow system on water main.
Air conditioning maintenance. Cleaned. tested and reset to factory specs for peak performance two air conditioner units. Replaced sump pump. Tested and cleaned up.
Bathroom plumbing repair. Toilet repair. Replaced flapper and tightened seat down. Inspected sump pump operation.
Repaired leak in filtered water line
Clean and check two newer Amanda furnaces. Also replaced media filters and humidifier pads. Checked sump pumps, battery backup system and water heaters.
Burr Ridge air conditioning clean and safety check. Reset two AC units to factory specs for proper operation. Reduce damaging electrical start-up surge by 50%. Extends system life, lowers utility bill with hard start kit.
Commercial air conditioning maintenance service. Reset to factory specs. Operating well.