Very personable and knowledgeable technician.
The technician came to conduct our semi-annual exhaust hood inspection. He was polite and considerate of our circumstances, we have a pre-school operating at the location and needed to conduct the test quickly without causing any anxiety for the children. He was very accommodating and moved quickly to silence the alarm as soon as systems functions were validated as working properly. A great experience.
August 20th ahmed/8am/ service with hood. Portable Extinguishers and Kitchen Suppression Inspection Annual Inspection Extinguisher Equip Desc: Inspect (3) Extings Ansul R-102 3-gallon: Semi-Annual Kitchen Inspection Equip. Desc.: ANSUL 3-gallon
123 harmony sw. vienna 22180 10-11a jim can be done later, no cooking currently. Kitchen Suppression Inspection Annual Inspection Dept: KITCHEN Equip Desc: (1) RANGEGUARD 2.5 GAL & (4) EXT **SEASONAL** Alarm Int: No Inoperable Deficiency for RangeGuard Unknown 2.5 Gallon: Same deficiency’s remain from last inspection No alarm or bell interlocked to fire suppression system Fryer lacks protection
1-5lb due Portable Extinguishers Inspection Annual Inspection Dept: EXTING Equip Desc: (4) EXT (KITCHEN-COMBO) Deficiency for 6L K Class Snack bar: K-guard located in the snack bar is due for hydro testing