The service was Class A. Thank You.
Repair service was considerate of our need to restore safety in the building as soon as possible. Mr. Bell exerted effort to correct an error (in material ordered) to accomplish the repair as scheduled.
Efficient service. Timely arrival.
Always reliable and prompt services.
8/31 Scheduled with Adriel 240-418-9822. Please call him about an hour before you arrive as he will be meeting you there. 12-4 Portable Extinguishers Inspection ***NEW CUSTOMER 8/2017*** Annual Inspection Extinguisher Equip Desc: Inspect Exts
Portable Extinguishers Inspection
Debbie 10a Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 3 GAL Alarm Int: Yes Deficiency for Ansul R-102 3 Gallon Left of hood: Ansul 3 gallon: 3 gallon cylinder is due for hydro testing MFD 2009 also regulator test is due. Cartridge: 101-30 MFD 2013 Inoperable Deficiency for Ansul R-102 3 Gallon Left of hood: Ansul 3 gallon: corrosion found in suppression lines. Note: system needs to be flushed with “Ansul flush” and purged with nitrogen to clear all blockages.