Crew is top notch. Work is professional and orderly. Received favorable comments from my tech who is working directly with the crew.
Techs are well trained and professional.
We have a lot of floors, nooks and crannies to search for fire extinguishers and Brian was thorough and super pleasant to deal with!
RANA 10-1030A Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Equip Desc: (3) EXTINGUISHERS Semi-Annual Kitchen Inspection Equip Desc: (1) RangeGuard 4 Gallon System Inoperable Deficiency: Same deficiency’s remain from last inspection: Electrical shock hazard on pizza oven system no longer ul300 compliant. **System past due for hydro testing (2004) was the last hydro test. **No alarm tied into system. **Exhaust fan not tied into system. Note: System upgrade needed!