Cool Air Solutions really take care and ownership in the condition and operation of our heating and cooling system. They provide a detail summary of the condition of the equipment and the life expectancy of parts so that we can plan our budget.
Jimmy did a great job and clearly explained everything that was be done.
Professional rep courteous explained what he did
Cool Air came through once again with fantastic service for my air conditioner. Troubleshooting and repair is their specialty.
Mateo and Nathan were great. Thank you.
The service was so great what more can I say
Although tech explained everything he found and recommended - AC is still not working right! Not fixed. Tech said he was calling back tomorrow after talking with manager.
Tech arrived on site and started installing the phenomenal air and the surge protectors. Once installed registered the products. Walked homeowner through setting up the fan settings. Unit is cooling upon departure.
Added refrigerant to a system that has a Schrader core issue last week. System is reading normal operating pressures and subcool per the manufactures data sheet.
Performed tuneup of a Goodman furnace. Heating temp split is 47 in range. Combustion blower is amping in range. Ignitor is reading within spec. Flame sensor was cleaned and reinstalled. Primary blower motor is balanced and amping under the max specifications at this time. System is equipped with a merv filter rack. Filter is ok at this time. Electrical compartment was cleaned as well as then unit itself. System was cycled before departure. Performed maintenance on a Goodman condensing unit. Condenser coils were chemically cleaned. Fan motor is free if any oil leaks and is balanced well. Systems starter is showing signs of pitting. Primary start control is reading within range. Condensate lines are free and clear of any blockage. Compressor is amping ok. Temperature split in cooling is 23. Refrigerant levels are ok. System is not protected.
Performed Heating maintenance on a 2018 Lennox furnace. Systems temp rise is 42 degrees in range. Primary blower motor is amping within manufacturers specs. Flame ignitor is reading within range at this time. Combustion blower is amping ok. Flame sensor was cleaned and reinstalled. Unit is not protected. Performed maintenance on a Lennox condenser unit. Condenser coils had mild dust buildup, it was washed off and reassembled. Condenser and fan motor amps are in range. Start amps for the compressor are ok. Single start motor is reading in range. Starter is ok. Refrigerant levels are in range for the unit. Cooling Temperature split is good at 20 degrees. Outdoor unit is not protected.
Returned to replace defrost control board and defrost temperature sensor. Tested equipment on cooling and verified operation. System is working properly at his time.
18-Month 0% interest available or 2% cash discount
Technician arrived on site and started performing 2 AC tune ups on 17 and 18 year old trane units. Started in the attic and checked air flow and ducts, and the blower compartment. Once done, went outside to the condensers and opened up the fan motor. Started cleaning the condenser coils. Once clean, started the units. Took amp readings and checked refrigerant charge. Cleaned out electrical cabinet and checked start components. Both fan motors amping high for it begin cold outside. The fan motor for the kitchen unit is almost over amping. Compressor start amps on kitchen unit was drawing LRA at 159. Max is 148.
Rewired the low voltage wiring at the heat pump, indoor fau and thermostat to function on a call for cooling.
Performed diagnostic on commercial unit. Age unknown, model and serial numbers no longer visible due to the sun. Owner states that system is not cooling, and temperature goes up instead of down. Cycled system for cooling. Checked rooftop unit electrical and components. Indoor blower motor is running , but compressor and condenser fan motor are not. Checked for power and found unit tripped on high pressure. Reset switch and system came on and started cooling. System ran for 5 minutes before cutting off on high pressure again. Found filters inside the unit were extremely clogged up, as well as unit also has 3 20x20x1 filters inside the salon that were also dirty. Removed filters inside the unit as they were the worst ones and reset unit. System came on and started cooling. Refrigerant levels are normal now and system ran with no problems for about 30 mins. Did not have filters to replace the inside with, owner will have her husband replace them Offered maintenance program, but units on
Performed furnace maintenance on a house with 2 Lennox systems. Left wing of the house duct runs are tight and free of any obstruction. Condensate lines are clear. Combustion blower is amping within range. Flame sensor was cleaned and reinstalled. Primary blower motor is leaking oil which is a sign of failure. Ignitor is reading out of range. Temperature split is right in range. The Right wing of the house needs a upsize in duct going to one of the rooms. Combustion and primary blower motors are in range and spinning freely. Ignitor and flame sensor read in range and were cleaned. Duct runs look tight and free of obstruction. Single start control is also reading within spec. Both units were were cycled before departure.
Returned to install drain pan. Installed new drain pan and reinstalled fittings, could not locate disconnect pull out switch, Per Dan it was ok to replace with a new Disconnect. Ran system and tested. System is operational upon departure. Left breaker in the off position. Office to bill for $1550 for drain pan and $400 for disconnect. $1950 total due.
Performed AC and furnace maintenance free with install. Maintenance checked out properly. Refrigerant pressures were measured and weâ€™re in the proper range. Amperage is for compressor and fan checked out. Cleaned off condenser coil. Furnace filter was replaced with homeowners. Recommended that maintenance plan is continue to maintain Systems standard. Upon departure system is fully operational in Heating in Cooling.
Add Supply to Kitchen. Permits and HERS testing included.
Performed combo tune up on 4 year old Bryant system. Cycled system for heating and cooling. Heating vent tube was not leveled correctly. Leveled pipe and also took out water that was sitting inside of it. Filter is still clean. Checked outdoor unit electrical and system components. Performed outdoor condenser clean. System is operational upon departure.
Upon arrival performed sensi predict install on second property. System was reset tested and fully functional upon departure.