Crew was on time and very professional.
Very thorough and good communication with customer
Everything was great. Really professional yet personalable
These guys are the best, polite and professional.
The service tech did an exceptional job checking the units
Performed AC and furnace maintenance
Turning the unit around.
Replace existing system with below listed equipment. 10,017 Due upon completion. Lowes 5% Off -$500. After all rebates and discounts $9,517
Replace existing 2-Ton Heatpump split system with below listed equipment. Lowes Card Options = 5% Off or 12 Months 0% interest or 36 Month 5.99% or 60 Month 6.99% or 84 Month 7.99%
Arrived on site to do combo maintenance on a 2018 Lennox system. Condenser Unit located in back yard furnace. Client stated no issues. Cycled system to ensure system operating. Found flex ducting used. Did heating maintenance. Inspected indoor unit in heating mode. Sequence of operation is good. Flame is good. Inducer motor amps are in range. Safety float switch, drain pump, and all other safety switches are operational. Temperature rise is in range. Cycled system. Cycled in cooling mood. Found filter dirty. Recommend replacing filter to reduce amount of dirt entering system. Blower wheel is good and clean at this time. Motor is good. Evaporator coil is clean at this time. Drain lines are good. Safety float switch is good. Drain pump is draining. Temperature rise is in range. Washed unit inside and out. Checked electrical compartment and connection. All was good. Primary and secondary motor control are both in range. Compressor and fan motor amp drawls in range. Refrigerant pressures a
Arrived on site on to diagnose a air flow issues on new system install. Client stTed there. It getting good air flow in master bed room. Inspected attic and ducting and temperature split. Checked to ensure dampers are open. System is a upflow in garage return vent 1st floor on the ground. System and master bed room are across from each other duct run. Got temp of 54 degrees From start of duct run. Got 55 degrees coming from master supply vent. Attic holds a lot of hot air not enough ventilation to remove heat in attic and help reduce heat load in home. Unable to increase CFM on blower due to having a a M30 thermostat. Advised loss of air flow is due to all the other ducts that break off to the other rooms are getting air flow first and by the time it reaches the farthest room there is loss of air flow due to the traveling distance. Advised client there is nothing i can do at this time. will be talking it over with office to see what can be done to improve air flow. Client is aware. S
Upon arrival turned systems on power on, showed customer how to install thermostat. Said contractor is putting on grills they werenâ€™t done with work. Customer took thermostat off and keeping it off till house is done.
Cooling maintenance and service, checked under home ducting for air leaks.
Getting a system up and running out here in San Diego
Inspected the HRV for bugs and seal
Performance tune up for the Ac system
odor inspection for heating system
18 Months 0% interest or 120 month 6.99% Payment plans available $17,900 due upon completion. After Lennox rebate total $16,750 Escrow to pay $11,855 Customer to pay $6,045 Lennox rebate paid back to customer $1,150
Upon arrival performed ac maintenance. Outdoor motors are leaking oil and starting to work harder then normal. Refrigerant levels are good. Primary controls are rusting up and recommend replacing, not replacing primary controls can cause the system not to run or start. Disconnects are stuck and donâ€™t come out unless you fully force it, did not force it advised customer that is not safe for technicians to come out and service. Turned off breaker for ac units to service. Customer does not wanna replace systems, moving from home in 2 years.