Each time Jorge came to our house he was friendly, conscientious and always professional. He reached out to Lenox and made sure we were covered under our warranty.
Pleasant and willing to do what I needed to complete the job. Worked with me to get the best price possible.
Answer all are questions. Was very polite and professional. Was happy he put on covers on his shoes even though our front yard is having a work over. Also he wasn’t in a hurry to finish the job. We would definitely ask for him to check our AC. Very good quality work. 10 stars !!!
Cool Air Solutions really take care and ownership in the condition and operation of our heating and cooling system. They provide a detail summary of the condition of the equipment and the life expectancy of parts so that we can plan our budget.
Jimmy did a great job and clearly explained everything that was be done.
Performed furnace maintenance on a 2015 Lennox gas furnace. Customer reports good working condition prior to visit. System is heating high but in range. Filter is very dirty. Sensors cleaned and tested. Primary blower and combustion blower are reading in range. Gas valve and ignitor were tested and recorded. Condensate lines are clear, pump is operational. Furnace compartment and closet were vacuumed out. The furnace power source is connected only to a light switch which provides no protection. Recommending hard wired equipment protection that will protect the furnace as well has the smart hub and thermostat. Filter was replaced today. Homeowner is aware of the condition of the unit. System is operational.
Performed heating maintenance on a 2019 Lennox gas furnace. Systems flames struggled to stay on when first cycled on. After sensors and switches weee cleaned this issue was resolved. Systems heating temperature rise is high but in range. Filter is clean. Combustion blower and primary blower are reading in range. Gas valve and ignitor were tested. Condensate lines are clear. System is not protected. System is operational at end of appointment.
Performed heating maintenance on a 2019 Lennox gas furnace. Temperature rise is in range. Sensors and switches were tested and cleaned. Primary blower Anaâ€™s combustion blower are reading in range. Filter is clean. Gas valve and ignitor were tested and recorded. Static pressure is right in range according to spec. System is not protected. Wife wants an email sent to homeowner so he can consider protection options. System is operational.
Quote to add 3 returns, no ducting open soffit returns, one in living room and two in upstairs hallway.
Installed indoor blower motor and single secondary motor control. Parts warranty for 1 year
Performed furnace maintenance on 2012 Rheem heater. During the maintenance they were a few points of concerns that were addressed with both homeowners. 1. Indoor Blower motor has significant oil leakage occurring, Itâ€™s left in this condition and it worsens this can lead to the motor potentially locking up or even overheating. 2. Single secondary motor control is weak due to indoor blower motor using too much power 3. System is not equipped with surge protection in the case of a power outage thunder storm, surge etc. 4. Flame sensor was cleaned and spark igniter is in good condition 5. Filter was swapped out and Is swapped out every three months Discussed and informed the full condition of Bobâ€™s 2012 Rheem heater. Clients would like to do preventative repairs and will be ordering indoor blower motor and installing once part is in hand. surge protector was installed at time of appointment. Upon departure System and Operational and Heating and will be calling once part is at the ware
Preformed heatpump maintenance on 2019 Lennox unit
Heating Maintenance Performed Upon arrival system is working and operational. I began my maintenance in the attic by performing a duct leakage inspection. I then proceeded to the furnace unit, I checked and tightened electrical connections. I inspected the heating components for proper operation and wear. Burners were inspected for proper operation. Flame sensor was cleaned. Condensates lines were inspected for proper drainage. Static pressures and temperature splits were taken. Filter has been checked, does not need to be changed at this time. Blower housing and wheel was inspected for balance and dust build up. Air supply was measured. Inspected safety switches as well as inspected home for fire and carbon monoxide detectors. Phenomenal was checked for operation. Upon departure system is working and operational.
Performed AC Diagnostic on 1994 comfort maker condenser. Upon arrival client was referred By another client. Clients are selling and moving out within a month and recently had the home inspector come by and imeasure the temperature split on the air conditioning unit and found that it was below the 14 to 22Â° Tempsplit. Upon arrival found that the breaker was not supplying the full leg of power to the condenser at the outdoor unit. 1994 comfortmaker 1. Breaker was not supplying 2 legs of power to the outdoor condenser. 2. Amperages on compressor on the brink of over amping 3. System was slightly low on R22 refrigerant. R22 was completely phased out January 1, 2020. 4. Duel secondary motor control is becoming weak 5. Outdoor condensing fan motor has significant oil leakage coming from itâ€™s bearing and can potentially lead to a locking up overheating 6. Condenser coil has minor dents in it Discussed and informed the full condition of Garyâ€™s 1994 comfortmaker Unit. At this time they w
Performed Ac/furnace maintenance on 2020 Lennox system.
Performed Ac maintenance on 2 system 2001 Lennox condenser. Upon arrival client stated the heater for downstairs unit was not working he noticed 1 week ago. Found the gas valve was left turned off from last maintenance. Heater is fully operational. Living room side system- 1. Compressor amps are pushing near max. Compressors is 24 A at this time. This will put the compressor at a higher risk of failing 2. Condenser fan motor is over amping and leaking oil from bearing 3. Duel secondary motor control is weak on hermetic and fan side 4. System Contains R22 refrigerant which was completely Phased Out January 1, 2020 5. Starter is slightly pitted on contact points 6. Condenser coilâ€™s banged up and in rough condition 7. System is not equipped with surge protection Indoor and out Right side system bedroom- 1. Compressor is also beginning over amp along with the fan motor 2. Fan motor is leaking oil 3. Duel secondary motor control this weak 4. System also contains R22 Informed and discussed
Upon arrival performed maintenance on Lennox heating and air system. Opened up door panels and washed coils out with chemicals. Opened top of condenser and cleaned out caging. Refrigerant levels are in range. Compressor is starting with high amperages. Recommended adding booster kit to keep amperages low. Secondary motor control in range. Filter was replaced client provided. System is operational upon departure.
Install compressor under warranty. Pressurize system with nitrogen in pulled vacuum down to 500 microns. Charge system up with approximately 10 pounds R410a. System is now operational and cooling home.
Arrived on site to perform fall tune up on a 2021 AcPro unit. Home was built in the 50s but found unit to have been replaced. Home only has heater. Cycled unit and was operational. Found filter be replaced. Blower assembly is good. Motor is good and in range. Inducer motor is good and in range. Flame sensor is good. Igniter is good. All safety switches are operational. Inspected attic and found all original metal ducts with a lot of leaks on connections. Insulation is coming off. And ducting are just small due to not a big home. Advised alot of rat poop in attic. Found asbestos B-vent for heater and water heater due to it being original from age. No protection on unit. Found gas flex line is going to unit to gas valve no sediment trap. Advised may be a safety concerns with inspection. Cycled unit and went over all findings with selling agent and she stated she would talk it over with new owner of home. Cycled system and unit is operational upon departure.
Arrived n site to return to install a new s 30. Installed new s30 that is purchased from us. Cycled new thermostat after install. Showed clients how to use new thermostat and connected phone. Clients are happy with new thermostat. Recommended surge protectors on both inside and outside for best protection. System is operational upon departure. Gave client back his whole complete s30.