Crew was on time and very professional.
Very thorough and good communication with customer
Everything was great. Really professional yet personalable
These guys are the best, polite and professional.
The service tech did an exceptional job checking the units
18 Months 0% interest or 120 month 6.99% Payment plans available $17,900 due upon completion. After Lennox rebate total $16,750 Escrow to pay $11,855 Customer to pay $6,045 Lennox rebate paid back to customer $1,150
Upon arrival performed ac maintenance. Outdoor motors are leaking oil and starting to work harder then normal. Refrigerant levels are good. Primary controls are rusting up and recommend replacing, not replacing primary controls can cause the system not to run or start. Disconnects are stuck and donâ€™t come out unless you fully force it, did not force it advised customer that is not safe for technicians to come out and service. Turned off breaker for ac units to service. Customer does not wanna replace systems, moving from home in 2 years.
Installer to go back out and install missing dampers downstairs.
Performed Fau maintenance on York furnace. Cycled furnace for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Evap coil is clean. Blower wheel is extremely dirty. Amp draws on blower motor are slightly high. Pressure in system was fairly high. Found 2 registers completely shut off. Spoke to Phyllis and recommended that they be open. Opened both registers and pressure did drop but still fairly high. Ductwork is original to home and fairly undersized. Verified heating components are working accordingly. Cleaned out heating compartment. Merv 11 filter is dirty and needs to be replaced. Replaced with approvaal. Went over findings and recommendations. Also recommended ESA Renewal. Could not get a hold of older sister to get a decision made, they are not sure what they are going to do with the house. Emailing invoice over to Roseanne with options and recommendations provided on todayâ€™s visit. Cycled system, system is operational
Upon arrival performed stat install.
Day 2 of install
Performed inspection and maintenance on both ac and heating systems
Upon arrival found bad thermostat, blank showing no signs of life. Tried replacing batteries. Circuit board is in bad condition. Signs of burnt terminals. Coming back to do thermostat.
Doing a single system heating and cooling maintenance out here in Mira Mesa
Performed fau Maint on 6 year old Lennox 98% furnace. Cycled furnace for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is high, and system was going off on high pressure. After inspecting unit, found a very dirty Merv 16 filter and very dirty 1 inch filter which was restricting system of airflow. Removed 1 inch filter from return cabinet, and replaced Merv 16 filter with filter provided by homeowner. Cycled system and system ran with no problems. Amp draws are normal. Blower wheel and Evap coil are clean. Tested and verified safety components. Wiped down heating compartment. System is not surge protected. Cycled system, system is operational upon departure.
Day 2 of install
Full system install
Follow up next week. They had costco out and have 2 others coming out
Furnace checkup to ensure proper reliable operation.
Upon arrival performed maintenance. Insulation levels are very good in attic. Filter was replaced. Not one spec of dirt inside of unit. Duct work is brand new and nicely strapped. Circuit board and electrical connections good. Blower wheel good. Amperages throughout system good. Temp rise is good. System was reset tested and fully functional upon departure.