Each time Jorge came to our house he was friendly, conscientious and always professional. He reached out to Lenox and made sure we were covered under our warranty.
Pleasant and willing to do what I needed to complete the job. Worked with me to get the best price possible.
Answer all are questions. Was very polite and professional. Was happy he put on covers on his shoes even though our front yard is having a work over. Also he wasn’t in a hurry to finish the job. We would definitely ask for him to check our AC. Very good quality work. 10 stars !!!
Cool Air Solutions really take care and ownership in the condition and operation of our heating and cooling system. They provide a detail summary of the condition of the equipment and the life expectancy of parts so that we can plan our budget.
Jimmy did a great job and clearly explained everything that was be done.
Professional rep courteous explained what he did
Performed tune up on 2 trane systems checked electrical, checked charge, checked temperature splits and washed down both condensers.
Upon arrival performed s30 thermostat installation.
Performed combo m maintenance on a 2021 Lennox system. Refrigerant levels were checked and verified in range. Electrical amp draws show healthy components. Filter was changed today. Scheduled maintenance was setup for the following year. A vibrating panel was fixed today.
Performed maintenance on a Lennox condenser. System was chemically washed. Electrical amp readings show healthy working condition. Refrigerant levels are good. Filter is clean at this time. Both units are not protected. System is operational at end of appointment.
Upon arrival started ac tune up. Condenser had a light coat of dog hair. Washed it out. Tested electrical and refrigerant charge. Found no issues. Temp spit is good. Temp split between upstairs and downstairs are high. Advised client of how itâ€™s designed. Upflows generally donâ€™t perform the best and we would need to relocate the unit to the attic. Unit is operational upon departure.
Upon arrival, started tune up of system. Cleaned condenser coils and bottom of condenser. Checked charge and itâ€™s good. All electrical is good. Compressor amps slightly higher than previous visit. Still within range. Static pressure is GREAT. unit is getting maximum airflow. Insulation came out fantastic. No filter change needed at this time. No issues found on inspection.
Upon arrival performed AC maintenance. Cleaned condenser coils out completely. Wiped furnace cabinet off. Circuit board and electrical connections good. Replaced filter client provided. Ducting in very well condition. Amperageâ€™s throughout system in very good standing. System has no protection. Although in very good condition. System is operational upon completion.
Upon arrival performed AC maintenance. Refrigerant levels are in range. Washed out condenser coils. Compressor has a Hardstart. Secondary motor control in range. Electrical fuses good. Indoor blower wheel clean. Cycled system on & off. Overall system in very good condition. Couple things that can be added to help systems longevity. System is operational upon completion.
Preformed ac maintenance on heatpump Lennox
Measured lineset for new location and provided price for work. Need to return with additional technician. Measured lineset for new location and provided price for work. Need to return with additional technician.
Performed Combo tune up on 4 year old Maytag unit. Replaced filter. Thoroughly washed out condenser. Checked electrical and system components. Refrigerant levels in Range. System is operational upon departure.
Replaced foam covering on lineset. And re enforced with UV protectant tape as lineset covering was chewed apart by dog.
Performed ac and furnace maintenance. Checked electrical components. Inspected safety mechanisms on units. Determined there was no surge protection on outdoor unit. Checked filter. Cleaned and checked flame sensor. Cleaned and removed debris from outdoor condenser unit. System is operational in heating and cooling mode.
Arrived on site to perform to System Lennox AC maintenance. Upon arrival client supplied filters for both upstairs and downstairs. Maintenance checked out properly. Measured refrigerant pressures and found that both systems were in the proper range. Measured Amperages for compressor and fan and both were in range at this time. Upstairs and downstairs condenser coils were both cleaned. Systems were not equipped with surge protection. Verified no water is present in emergency pans up inside attic. Upon departure client is aware of current condition of System and System is fully operational