Professional rep courteous explained what he did
Cool Air came through once again with fantastic service for my air conditioner. Troubleshooting and repair is their specialty.
Mateo and Nathan were great. Thank you.
The service was so great what more can I say
Although tech explained everything he found and recommended - AC is still not working right! Not fixed. Tech said he was calling back tomorrow after talking with manager.
Crew was on time and very professional.
Two system heating tuneup. Cleaned filters. Tested voltages. Inspected Ted duct connections. Cleaned condensate traps. Recorded temperatures. Verified charge.
Returned to replace pan. Removed existing cracked pan. Found that pan that was sent to us was the wrong size. Spoke to Goodman and the correct pan will be sent to us, will return To install. Made Dan aware, will be in contact once we get correct pan.
Arrived back on site to return to do service repairs on 2 Trane systems. Client is aware of repairs is done of 2 Merv racks, 2 plenums, 2 igniter ,2 flame sensors ,2 blower cleanings ,2 secondary motor controls. Client approved of repairs done. Was happy with service. Cycled both systems in heating and cooling both systems are operational. Both systems are operational,heating and cooling upon departure.
Arrived on site to perform fall tune up on 2 2003 trane system located in attics. Client stated no issues and wanted inspection done. Cycled both thermostat and good. Found both filters dirty allowing dirt to enter system. Recommend upgrading filters to merv 16 racks to filter a lot more to both system Would need at add plenums to Seal properly. New flex ducting used and okay. Both blower assembly really dirty creating stress and wear on motors. Recommend assembly cleaning to reduce how hard motors are working and high amp drawls. Amp drawls are in range on both but going to high side as they operate. Motors are staying to leak oil from self wear and stress accumulating and developing over past years. Found secondary motors both out of range and weak from motor draining life of component. Recommend replacing to prevent motor from not operating. Inspected both heat exchanger and found both covered in heat impingement from over heating.no cracks on both just heat impingement all ove
Re wired unit ran test both heat and cool everything works. Showed home owner how to use t stat
Combo Maintenance and installation of Sensi Predict
Performed heating tune up on Carrier system. Met with tenants. Cycled system for heat. Verified proper heating sequence of operations. Checked electrical and heating components. Cleaned off blower wheel assembly as well as heating compartment. Cleaned flame sensor. Ran system through 20 point inspection. Indoor blower wheel is dirty, and motor has started to leak a significant amount of oil. Secondary motor control within range. Gas pipe has no sediment trap.,pulled limit switch and evap coil cover to inspect heat exchanger. Filter is extremely odd size, advised tenant to replace at earliest convenience as it was very dirty. System is operational but is very old and very inefficient. Tried contacting homeowner but calls going straight to voicemail. Will email invoice and findings over. System is operational upon departure.
Inspected outdoor contactor for buzzing. Adjusted low voltage spade connection and tested across coil for proper resistance. Inspected contacts for pitting. Contactor is okay.
Install S30 due to defective Icomfort covered under warranty
Install listed furnace. Replace 5 attic duct runs. Permits and HERS testing included. $7,469 paid to Loweâ€™s. Customer receives $175 from Lennox bringing total to $7,294 0% Finance Options= Loweâ€™s Card 12 months 0% interest or Service finance 18 months 0% interest
Arrived on site to perform fall tune up on a 2017 Lennox system. Furnace and Evaporator coil located in attic. Client stated no issues just wanted filter checked out. Cycled heating mode and system operational. Found new ducting used and good condition. Filter is dirty which is causing airflow restriction in system. Recommend replacing filter to prevent air flow restrictions and reduce amount of dirt entering system. Blower assembly is good light dust. Wheel is good. Blower motor good. Amp drawls on both blower and inducer motor are both good and in range. Evaporator coil is good at this time. Heat exchanger is good. Drain lines are good and draining. Temperature rise is in range and heating. Recommend adding a whole house cleaning and purifying system to help keep system and home clean as well purifying air in home for a better air quality. No protection on high efficient systems. Recommend adding a surge protector on unit to protect it from getting damaged but electrical shortages
Performed AC/furnace maintenance on 2012 carrier system. Upon my maintenance there were a few points or concerns that need to be addressed. 3 ton carrier condenser downstairs- 1. Found a secondary motor control was becoming Week on fan side and hermetic side terminals 2. Condenser fan motor slightly leaking oil from bearing 3. High voltage really showing signs of pitting and burn marks about 90% on contact point 3 ton carrier condenser upstairs- 1. Also found that secondary motor control was becoming week on hermetic and fan side terminal 2. High voltage really showed about 75% pitting and burn marks on contact point 3. Condenser fan motor has leaked out a significant amount of oil from bearing 4. Motor is coming close to over amping from whatâ€™s recommended on specification of data plate. Furnace upstairs- 1. Flame sensor has developed carbon buildup and formed a green coat, This can interfere with heating start up 2. Found multiple heat spots located on heat exchanger due to low
Upon arrival performed maintenance on 1 year old lennox system. Verified system is in working order. Cycled heat on and off. Replaced filter that client provided. Dusted off electrical components and wiped down furnace cabinet. Amperages throughout system are in very good condition. Advised customer to start using merv 16 filter for higher grade filtration. Indoor motor and wheel are in very good condtion. Amp draws on compressor & fan motor are in very good conditon. Refrigerant levels good . Temp splits good. Coils are clean. Dusted all electrical components inside of service door for ac. Secondary and primary motor controls are in very good condition. Was not able to fully wash condenser, water hose was not long enough to get to condenser. Cycled system on and off, system is in very good condition, install good did not need to fix anything . Disconnect and whip good. Fuses good. System was reset tested & fully functional upon departure.
$800 Lennox rebate back to customer brings total down to $25,210
Remove existing furnace and plenum and install new high efficiency Lennox furnace and evaporator coil. Properly plumb drain lines. Clean and flush existing refrigerant lines. Extend lines to existing rooftop pad. Add quad breaker in panel for 220v electrical run to rooftop. Crane service included 25 ft up and 40 ft in. (Crane service will be larked in front of garage 1,2,3 for 30 minutes for the ac lift to rooftop. Loweâ€™s card 5% discount (-$495) after discount $9422.00