My technician was very polite, and pleasant to deal with. He did a great job and was very thorough.
First of all I thought when they were coming out for an estimate it was only gonna be $100 I wasn’t aware that if it took two hours or three hours which the time was it written down correctly that it was going to cost me 300 I was quoted $99. Second of all it took three visits and after three visits they were talking thousands of dollars I could go on and on but my air-conditioning was fixedAt a cost of $1400 not the estimated thousands of dollars they were telling me
Dave provided a great service and his experience and workmanship showed in diagnosing and correcting an issue the previous installer had created. Very knowledgeable and an outstanding technician.
Jimmy came and diagnosed another condensation leak, fixed it and guided me though the process of isolating where the leak was from and steps to take to eliminate the cause.
Found water leaking from Condenser in attic, scheduled appointment and was there next day. Jimmy did an incredible job, was able to isolate the problem and fix it quickly and professionally. Very happy with the service!
We got our entire HVAC system updated and installed two years ago with Cool Air Solutions. They also helped us get new, energy efficient windows, which qualified us for a state rebate. From the technicians who handled the install to the service providers in the office, every person went above and beyond. When the city came to inspect and sign off on our project, the inspector said he’d never seen a cleaner install and asked us to pass on Cool Air’s info since he needed to update his own HVAC. Here we are two years later for our complimentary service, and the same high standard of care and service is clearly evident. Thank you to the office team for following up and reminding us about our service, and to Jorge for being a great technician!
Jorge was very thorough and informative in his diagnostic check of the A/C.
Very professional and knowledgeable
He was friendly, knowledgeable, and did it good job.
ServiceWas just as described Michael came out and did a thorough inspection and maintenance on both my units. He was courteous and professional. I would have cooler come out again.
Replace both existing units with listed equipment. Replace and re-design all ducting including high flow registers. HEPA Filtration included on both indoor air handlers. Relocate condenser and run new copper and electrical lines.
Arrived on site to perform diagnostic on a 2019 trans system. Client stated she just moved in and havenâ€™t used system and got warming up she and to use it system turns on and no air flow. Client stated she think something is stuck of clogged or not connected. Cycled unit. System did Turn on and was operational. Blower motor was operating as you could hear it from return. Inspected filter and filter was so heavily Clogged that was not allowing any airflow into system so not allowing airflow to be produced cold into home. Replaced filter and inspected and system was cooling and now had airflow In every vent. Had client inspected and personally feel berms to feel air flow is coming out. Found some Registers are pointed toward the walls so not allowing great airflow to living room or circulate properly. Recommend adding surge protectors on units to protect from electrical surge and power outages that can damage or even short out systems and components due to being the type of system they
Financing available After Rebate $13,294.00
Installed high pressure switch at the outdoor liquid line. Wired low voltage wiring to zone board at upstairs fau. Tested system on heating. System is working properly at this time.
Performed txv and bi flow filter drier replacement. Recovered all existing refrigerant into recovery tank. Purged lines with nitrogen. Removed filter drier and outdoor txv. Installed new filter drier using nitrogen and wet rag. Tested the system with nitrogen at 350 psig for 20 mins and held. Removed nitrogen and vacuumed entire system down to 500 microns. Weighed in refrigerant charge using digital scale. Ran system in cooling and adjusted with sub cooling. Cooling working properly. Tested system in heating. System runs for about 1 min before heat pump shuts down and goes into a 3 minute delay, heat strips start and heat pump will remain de energized with no error codes displaying. Displays standard status flash â€œnot callingâ€. Preceded to ground all extra low voltage wires at the smart hub, heat pump and air handler. Changed the safety float switch from R thermostat to R heat pump. Contacted Lennox tech support line and diagnosed the problem. Must install high pressure switch at t
Inspected upstairs heat pump for faults. Tested refrigerant pressures in cooling and found low sub cooling value. Charged the system to achieve a 11 degree sub cooling per the system specs. Tested system is heating mode without heat strips and system shut off on error code 441, OD inverter outdoor compressor amp draw. The system runs great in cooling but fails to operate in heating leading me to believe the outdoor txv is faulty. Ordering the outdoor txv and advising a complete recovery and fresh refrigerant recharge by weight.
Upon arrival performed ducting estimate, client needs to run through his wife before making many decisions.
arrived on site to diagnose a upstairs 2017 heat pump. Client stated he had the heat strips in use and his electrical bull is really high due to then being in use. Found condenser heat pump for upstairs has a bad txv valve and would needs to be replaced and filter dryer. Bad valve is causing heat pump to trip on high head pressure and after doing so 10 time condenser locks out and cause heat strip to get used for heating. Advised client labor is out of warranty. Would not recommend running System as itâ€™s just gunna use heat strips for heat. Advised client of find and repairs needed and he start heâ€™d rather get labor done and he would go about getting the refrigerant and recharging his system him self if he dose get repair of replacement of Txv and filter dryer. System is not operational upon departure due to repairs needed. Client did declined work at this time and will call office if he wants to go forward with repairs. System is not operational upon departure due to bad outdoor T
Upon arrival performed diagnostic on heating system. System is operational just takes time to kick on, system is very old, 30+ years. Systems lifespan is typically 12-15 years . Client wants estimate on ducts and full system replacement, weekends only work for client. Both home owners.
Upon arrival performmed heating maintenance on 2 year old Lennox heat pump. Replaced clients air filter. Indoor motor and wheel in very good condition. Evap coil is clean. Supply ducting does not have any seals, they are attached to plenum with no sealant. Advised client. Outdoor system in very good condition. RefrigerNt levels good. Washed outdoor coil. Took amp draws throughout system very good. Temp splits good. System was reset tested and fully functional upon departure. Signed client up with monthly esa with 4 filters yearly !
Performed heat pump diagnostic on 2002 Goodman system. Arrived on site to find system non-operational in heating mode customer stated this started happening a couple days ago. On initial start up heard indoor blower motor trying to start on air handler unit in attic. Proceeded outside to find outdoor condenser going off on high pressure due to no airflow across evaporator coil in the attic. Determined that single secondary motor control in attic is no longer supplying power to indoor blower motor this is what was causing no airflow in the system to go off on high pressure. Indoor blower motor has oil leakage and is overheating. Did a full inspection on outdoor unit and found that system contained R22 refrigerant which was completely phased out January 1, 2020. Found the high voltage is extremely pitted on contact points due to over amping over the years, This component access the brakes for the system and could potential fail if left in this condition. Found the duel secondary motor co
Leak repair and full system recharge
Arrived on site to perform repairs. Recovered refrigerant from unit. Sweated off existing txv and liquid line drier. Welded in new txv and line drier. Pulled vacuum down to 472 microns. Recharged with 10 lbs of R410 refrigerant. Cycled system through heating and cooling modes. System is now fully operational for cooling and heating.
Returned to install high pressure switch. Once installed, cycled system. Tested system in cooling mode to ensure refrigerant pressures are in range. Refrigerant pressures are good and system is producing a proper temperature split. Cycled system for heat. System kicks on but refrigerant levels are not where they are supposed to be and the system kicks off after running a couple minutes. Txv is creating a restriction in heat mode and not allowing system to properly heat. Need to return once valve and filter drier come in. Will need a helper. Cycled system, system is operational only in cooling upon departure. Collected $848 today, $1720 will be due upon completion.
Arrived on site to perform fall tun up on 2 2014 Maytag system. Units located in attic and other in garage. Client stated no issues just that the line set foam was coming off and would like to taken care off. Advised her I would take care of her today and retape line set with U.V tape to prevent foam from deteriorating more. Found both filters really dirty and replaced today. Recommend replacing more often as 3 months is rated for filters to reduce amount of dirt entering system. Both Blower assembly is good slight dirt accumulating due to having dirt filters in still and lack of changing them out as needed. Both systems amp drawls are good. Evaporator coils are both good just slight debris but good at this time. Temperature rise was good on both systems and heating. No protection on either units. Cycled system to ensure system operating. Washed both outside condenser inside and out to prevent air flow restrictions in system. Both units were washed and cleaned. Checked electrical compa