My technician was very polite, and pleasant to deal with. He did a great job and was very thorough.
First of all I thought when they were coming out for an estimate it was only gonna be $100 I wasn’t aware that if it took two hours or three hours which the time was it written down correctly that it was going to cost me 300 I was quoted $99. Second of all it took three visits and after three visits they were talking thousands of dollars I could go on and on but my air-conditioning was fixedAt a cost of $1400 not the estimated thousands of dollars they were telling me
Dave provided a great service and his experience and workmanship showed in diagnosing and correcting an issue the previous installer had created. Very knowledgeable and an outstanding technician.
Jimmy came and diagnosed another condensation leak, fixed it and guided me though the process of isolating where the leak was from and steps to take to eliminate the cause.
Found water leaking from Condenser in attic, scheduled appointment and was there next day. Jimmy did an incredible job, was able to isolate the problem and fix it quickly and professionally. Very happy with the service!
We got our entire HVAC system updated and installed two years ago with Cool Air Solutions. They also helped us get new, energy efficient windows, which qualified us for a state rebate. From the technicians who handled the install to the service providers in the office, every person went above and beyond. When the city came to inspect and sign off on our project, the inspector said he’d never seen a cleaner install and asked us to pass on Cool Air’s info since he needed to update his own HVAC. Here we are two years later for our complimentary service, and the same high standard of care and service is clearly evident. Thank you to the office team for following up and reminding us about our service, and to Jorge for being a great technician!
Jorge was very thorough and informative in his diagnostic check of the A/C.
Very professional and knowledgeable
He was friendly, knowledgeable, and did it good job.
ServiceWas just as described Michael came out and did a thorough inspection and maintenance on both my units. He was courteous and professional. I would have cooler come out again.
Arrived on site to perform repairs. Recovered refrigerant from unit. Sweated off existing txv and liquid line drier. Welded in new txv and line drier. Pulled vacuum down to 472 microns. Recharged with 10 lbs of R410 refrigerant. Cycled system through heating and cooling modes. System is now fully operational for cooling and heating.
Returned to install high pressure switch. Once installed, cycled system. Tested system in cooling mode to ensure refrigerant pressures are in range. Refrigerant pressures are good and system is producing a proper temperature split. Cycled system for heat. System kicks on but refrigerant levels are not where they are supposed to be and the system kicks off after running a couple minutes. Txv is creating a restriction in heat mode and not allowing system to properly heat. Need to return once valve and filter drier come in. Will need a helper. Cycled system, system is operational only in cooling upon departure. Collected $848 today, $1720 will be due upon completion.
Arrived on site to perform fall tun up on 2 2014 Maytag system. Units located in attic and other in garage. Client stated no issues just that the line set foam was coming off and would like to taken care off. Advised her I would take care of her today and retape line set with U.V tape to prevent foam from deteriorating more. Found both filters really dirty and replaced today. Recommend replacing more often as 3 months is rated for filters to reduce amount of dirt entering system. Both Blower assembly is good slight dirt accumulating due to having dirt filters in still and lack of changing them out as needed. Both systems amp drawls are good. Evaporator coils are both good just slight debris but good at this time. Temperature rise was good on both systems and heating. No protection on either units. Cycled system to ensure system operating. Washed both outside condenser inside and out to prevent air flow restrictions in system. Both units were washed and cleaned. Checked electrical compa
Performed heating maintenance on 7 year old heat pump unit. Cycled system for heat. Checked indoor unit electrical and system components. Indoor blower wheel and evap coil are clean. Motor looks healthy. Temperature split is within range. Replaced filter with filter provided by homeowner. Checked outdoor unit electrical and components. Amp draws are within range. Primary motor control is in good condition . Secondary motor control is within range. Pulled off condenser fan motor and thoroughly washed out condenser coil inside and out. Went over findings and recommendations with homeowner. Would recommend upgrading filter to a MERV 16 filter for better filtration. Cycled system, system is operational upon departure.
Returned to complete work. Replaced circuit board on downstairs unit. Tightened all electrical connections and secured wires. Cycled system through modes. In heat mode inducer motor is running at max amp capacity. Homeowner was made aware. System is fully operational upon departure.
System not functional on arrival. Outdoor compressor temp very high and system not heating. Attached gauges and adjusted refrigerant pressures. Tested system on both heating and cooling. Tested flare fittings at the outdoor heat pump and found no indications of leaking. No oil on walls below head units. System may have a leak somewhere but unable to determine location at this time.
Performed diagnostic on 4 year old Lennox system. Not heating. Cycled system for heat. Outdoor unit is unresponsive. Circuit board was showing error node for low pressure. Checked and found refrigerant level to be low. With approval charged system up with refrigerant. Cycled system with proper charge, low pressure switch is still not closing. Pressure switch is bad, need to order and return to replace. Will also be adding Leak Dye and Seal. Will be ordering part on Monday and will advise with eta on part. System is not operational. Collected $100 Today, $848 will be due upon completion of work.
Arrived on site to perform diagnostic on 2 13 year old Goodman furnaces. Homeowner states that neither of his 2 systems are not heating, Have not worked for about a month. Did mention that he did have a power outage before they stopped working. Cycled upstairs unit for heat. Heating sequence engaged, but cut off after the ignitor turned on. Circuit board flashing code for open pressure switch. Tested switch and switch is opening and closing as it should. Bypassed pressure switch and tried cycling unit, circuit board is still stuck on open pressure switch code. Continued resetting board until code finally cleared and unit kicked on. Circuit board is failing intermittently, would recommend replacing circuit board on this unit, but system is operational upon departure. Cycled downstairs unit for heat. System automatically goes into pressure lockout. Tested all pressure switches and they all open and close normally. Tried resetting circuit board numerous times and it still goes straight
Installed ecobee thermostat on heat pump system. Charged for labor for one hour. System is fully operational and compatible with new thermostat. Recommended the system is maintain due to age.
Upon arrival performed maintenance. Purged nitrogen through drain line. Indoor motor is good. Filter is in good condition. Recommend using Lennox made filter. Circuit board and electrical connections good. Safety switches in working order. Refrigerant levels good. Washed outdoor coils. Dusted off all electrical connections. Temp splits good. System is in overal great condition. System was reset tested and fully functional upon departure.
Returned to perform work. Added new condensation pump to primary line and added safety switch on secondary drain line. Wired in safety switches. Ran system to test condensation pump. Pump is operational and pumping water out of the line. Secured condensation pump. System running and operational upon departure.
System is leaking water into wall. Drain lines are not clogged. Bad fitting somewhere inside the wall. Will be running drain into a condensation pump , and run tubing for condensation inside the existing drain line that is going outside the home. Will be ordering pump and will let dispatch know when part comes in to schedule return call. Collected $91.00 deposit, $824.20 to be collected at time of completion.
Getting a system up and running out here in Canyon Lake
Upon arrival performed diagnostic. System is cooling has a 20 degree split. Indoor coil is very dirty and a lot of restriction. Duct work is original to home. Indoor motor leaking excessive amount of oil. Outdoor refrigerant levels look good. Amperages on compressor are 18 running amps. Condenser fan motor leaking oil. System has 2 wire hardstart kit. Replaced 20x25x1 filter. System needs repairs and deepmcleanings to get system to work properly. Home owner is working and will get with his team to look over repair options. Office to take diagnostic over phone please.
Arrived on site to diagnose air flow issue on a 3 zoned heat pump system. Inspected all zones and thermostat. Inspected attic and indoor air handler. Inspected system operation. Inspect out door unit. Che led refrigerant pressure and inspect ducting layout and duct sizes. The summary of findings are as followed. Air handler 1. Found no very low air flow to master room zone 1. 2. Found duct to master bed room to be undersized and not providing enough air flow to bedroom. Should have another return vent in home. 3. 4 ton unit with only 1 return on first floor and is under sized creating high static pressure within system. 4.Found air handler ducting to be using old gray flex ducting and is in bad condition as part of the ducting insulation is falling part losing cold temperature in attic. 5. Ducting lay isnâ€™t the best design for home and system for proper airflow. 6. Found 10 inch damper for zone 3 will not open or close allowing all cold air to go to zone 3 since it is always open